Electrical Panel Grounding Methods
Can I connect the ground wire to the same slot on the neutral bar and the white neutral wire since the grounding rod wire is already attached?
Electrical Panel Grounding Methods
Background: Pablo, a Homeowner from Mathis, Texas
Question: House has old 2 wire cable with no ground. Electric panel only has one bar. White neutrals are connected here as well as the wire going to the grounding rod – both in main service panel and sub-panel. Question – if I replace the old wire with new cable with ground wire can I connect the ground wire to the same slot on the neutral bar and the white neutral wire since the grounding rod wire is already attached? Or do I need to add a ground bar?
Thanks for your electrical question Pablo. At the Main Panel the Grounds and Neutrals all terminate together on the same terminal bar. In sub-panels all grounds must be separated from the neutrals which requires a separate ground bar to be installed directly to the panel frame or enclosure. Most panels are pre-taped for a ground bar to be installed if there isn’t one already. Neutral bars in sub-panels must not be bonded to the frame of the sub-panel enclosure. 240 volt Sub-Panels require a 4-wire cable feed to provide this separation between the neutral and the ground.
The Following links will assist you with your electrical question:
For more information about Grounding
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Videos
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Grounding and Home Electrical Wiring:|
|« Previous||Next »|
|Electrical Requirements for a Journeyman in Pennsylvania||Troubleshooting Bathroom Electrical Problems|