Electrical Code for a Bedroom Light and Switch
How Wall Switches and Light Fixtures are Wired for the Home
How Wall Switches and Light Fixtures are Wired
Question: We are purchasing a spec house in South Carolina. The builder forgot to install wiring for an overhead light in the master bedroom, but did provide a switch for the non-existent wiring. Our home inspector “thought” it might be required by code to have wiring for an overhead light, but he wasn’t sure. Can you help? Thank you. Jennifer
This electrical question came from: Jennifer, a Homeowner from Fort Mill, South Carolina.
See more about Home Wiring for South Carolina
Thanks for your electrical question Jennifer.
Wiring Switches and Light Fixtures for the Home
Electrical Code Requirement for a Bedroom Light
Jennifer, a wall switch must be located at the entrance to the bedroom on the inside wall, and it can either control a wall outlet that can be used for a floor light fixture or table lamp, or the wall switch could control a ceiling mounted light fixture.
NEC Code for Bedroom Light Switch
- 210.70(A)(1) Lighting outlets:
- Wall-switch controlled lighting outlets required in all habitable rooms and areas.
- 210.70(A)(1) Exception (1) Lighting outlets:
- Habitable room lighting outlets may be switched receptacle except in kitchen and area.
Wiring a Light Switch – Diagram 1
Fully Explained Light Switch Wiring Diagrams. Detailed Electrical Wiring Diagrams and Pictures assist your Home Electrical Projects.
Electrical Code Articles for Home Wiring
Electrical Code Directory covering AFCI circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, electrical GFCI, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-code, and smoke-detectors.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about NEC 210.70 Bedroom Light Switch and Home Electrical Wiring:|
|« Previous||Next »|
|Earth Grounding for an Electrical Service||Cause of Burnt Out Light Bulbs and Hot Cooking Oven|