Damaged Extension Cord Causes Outlets to Stop Working
How to Reset GFCI Outlets and Circuit Breakers to Restore Electrical Power: Locating and Testing GFCI Outlets and Circuit Breakers.
Cut Extension Cord and Outlet Problem
Electrical Question: I was using an extension cord and accidentally cut it, now some outlets are not working.
- I Have two GFI’s in my home. The one GFI outlet for the bathroom works fine.
- Recently I was using an extension cord and accidentally cut while it this was connected to an outside outlet.
- After it was cut four of my kitchen outlets will not work and none of my outside plugs worked. I looked in the kitchen, garage, and in the utility closet and did not find any GFI outlets that were tripped off.
- I checked my breaker box and none of the breakers were tripped. There is two different breakers for two separate GFIs. Where else could I look to find to find the problem.
This electrical question came from: Christin in California.
Thanks for your electrical question Christin.
Resetting GFI Outlets and Breakers
Locating and Testing GFCI Outlets and Circuit Breakers
- When the extension cord was damaged it caused a circuit protection device to trip off.
- This may have been a GFI outlet or a GFCI circuit breaker, or it may have affected a regular circuit breaker.
- Because you have noticed that there is no power to more than one circuit locations then I would recommend that all of the home circuit breakers be turned off and then turn of the main electrical service breaker as well because it is very possible that one of the main power circuits may have tripped off.
Restoring Electrical Power to the Home
How to Reset GFCI Outlets and Circuit Breakers to Restore Electrical Power
- To restore power make sure each circuit breaker has been pushed all the way into the OFF position, and then turn the circuit breaker back on starting with the Main electrical circuit breaker.
Testing and Resetting GFI Devices
- If the power has not been restored to the affected circuits then locate all of the GFI devices and press the TEST and RESET buttons to make sure that they have been reset and are functioning properly.
- If this does not solve the problem then contact a qualified licensed electrical contractor who will provide a series of test that will reveal the problem.
More about GFCI Outlets
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
GFCI and GFI Wiring Diagrams
The features and benefits of GFCI outlets and receptacles will give you a clear understanding of the importance why these safety devices are required by code to help protect you and your family against accidental electrical shock hazards.
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Troubleshooting, GFCI Outlets, Lost Power to Outlet and Home Electrical Wiring:|
|« Previous||Next »|
|Switched Outlet Wiring Diagrams||RCD and Freezer Fridge Outlets|