Can different voltages exist in the same switch box?
partitioning different voltages….
Electrical Question from Kolby about Electrical Wiring
Background: Kolby, a Electrician from Longview, TX
Question: Can you have a 120 volt switch and a 277 volt switch in same unpartioned switch box?
Thanks for your electrical question Kolby. The answer is no. A partition must separate the two voltages.
NOTE to Homeowners:Â This question applies to commercial and industrial wiring applications.
The Following links will assist you with your electrical question:
For more information about Electrical Wiring
This link is helpful as a Electrician
Electrical Code Articles
Make sure not to miss these Resources for: Other
Home Electrical Wiring Resources
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about Electrical, Electrical Code NEC and Home Electrical Wiring:|
|« Previous||Next »|
|What happens if my treadmill outlet is not grounded?||Why did my computer screen just turn green?|