Calculating Electrical Power Requirements
I am looking to lease a 5,000 sq ft building that has (2) 200 amp 3 phase 220/480 electrical panels feeding (1) 110/220 panel…
Electrical Power Requirements for a Commercial Kitchen
Background: Sarah, a Homeowner from Eugene, OR
[ad#block]Question: I am looking to lease a 5,000 sq ft building that has (2) 200 amp 3 phase 220/480 electrical panels feeding (1) 110/220 panel.
My business will supply four kitchens with full functioning commercial equipment. Ovens, microwaves, stoves mixers and more.
Up to four computers and offices.
Some of the equipment that will be used:
1 3 hp walk in cooler compressor
2 domestic freezers
hot water heater
washer and dryer
possibly an elevator (small non functioning right now)
Is the current power supply enough to support my current needs? And if so, is there enough power to add on more power in the future?
Thank you so much for your web site. This is the first time I have been on it. I can see that I will be using it a lot!
Thanks for your electrical question Sarah.
- The specified nameplate power requirements are necessary in order to determine the circuit voltage and amperage for each piece of equipment you have in this list.
- Understanding this will then allow one to calculate the total connected load. Some of this equipment such as the ovens and water heater may use natural gas or propane for heating which will make a big difference.
- The next factor would be to understand how many of the listed units will be operating at the same time in order to determine an estimated load on the main electrical service panel.
I have provided the following resources that lead to fully detailed information on this website that will assist you with your electrical question:
For more information about Troubleshooting
Troubleshooting Electrical Wiring
This link is helpful as a Homeowner
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Commercial, Electrical and Home Electrical Wiring:|
|« Previous||Next »|
|Considerations When Upgrading Home Electrical Wiring||Calculating Voltage Drop for an Underground Circuit|