Hot Tub Electrical Circuit Wiring and Requirements
Electrical Circuit Wiring for a Hot Tub Circuit: The electrical circuit is a dedicated GFCI protected circuit. Many hot tubs required a 4-wire circuit which has a separate neutral and separate ground along with the 2-conductors which provide the 240 volt circuit.
Electrical Wiring for a Hot Tub Circuit
Electrical Question: We have a ThermoSpa Hot Tub Park Avenue Executive outside on our deck that came with the house here in MA.
The hot tub requires 2 – 240v circuits, both 30 amps. It is currently wired with the following:
Main Electrical Panel:
1 – 30 Amp 240V GFCI
1 – 20 Amp 120V GFCI (incorrect, need a 240v)
Sub-Panel near the Hot Tub, outside:
Hard wired with a “big handle” type switch on the side, no additional GFCI, controls ONLY the 240V line.
- They originally hijacked the 240v supply for the Range, and added a GFCI breaker, but they did NOT connect the White load-wire to the GFCI and left it connected to the neutral\ground bar in the box (which I fixed).
- They did the same thing for the 120v GFCI breaker, so I moved the white wire to the breaker for that one as well.
- The white pigtails were connected to the ground strip on both GFCI breakers. (I hope all that makes sense!)
My questions about this Hot Tub Circuit Wiring are:
- Is it OK that the GFCI breakers are in the main box?
- Is it OK that there are no breakers in the Sub-Panel and just a large lever-type switch?
- Am I correct that all load-wires should be connected to the GFCI breaker (red, black, white), except for the ground wire?
- Is there any way to test the GFCI breaker other than hitting the “TEST” button (ie, short out the line at the Hot Tub)
- They used Aluminum Wire (heavy gauge). Is that ever OK? If so, what gauge?
Thanks for your help!
This electrical wiring question came from: Kevin, a Homeowner from Marlborough, MA
Thanks for your electrical wiring question Kevin.
Electrical Circuit Wiring for a Hot Tub Circuit
- A typical hot tub requires a 50 amp, 240 volt 4-wire circuit, but this could vary depending on the exact hot tub that is installed so the installation manual should be consulted.
- The electrical circuit is a dedicated GFCI protected circuit. Many hot tubs required a 4-wire circuit which has a separate neutral and separate ground along with the 2-conductors which provide the 240 volt circuit.
- Most hot tubs will specify that the electrical circuit wiring must be copper, not aluminum, I have replaced aluminum hot tub circuit wiring where copper was specifically required.
- A disconnect switch must be in the location of the hot tub. The switch does not have to have the GFCI circuit breaker, it can be a handle type disconnect.
Hot tub wiring
Hot Tub Wiring Diagram Information
Electrical Codes and Details for Spa and Hot Tub Wiring. Essentials for your installation, including the required gfci ground fault protection and circuit wire size.
The Following will assist you with your Hot Tub Circuit
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
Electrical Wiring Protection using Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about Hot Tub Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|How to Install Electrical Wiring in a Livestock Area||How to Install and Wire Your Ceiling Fans|