Adding Light Fixtures to 4-Way Switch Wiring
How to Wire a 4-Way Switch Light for Light Fixtures – The 3-wire that runs between does not have a neutral wire, and besides, you would not have the correct switching sequence as the final common to the light fixtures from the end 3-way switch.
Adding Light Fixtures to Existing 4-Way Light Switches
[ad#block]Electrical Question:Is it possible to have two light fixtures between four switches?
- In other words, can I do the following:
- Power into 3 way, then out to 4 way, then out to two lights, then to 4 way, ending at a 3 way?
- I know this is unusual, but I am doing an addition on my home and in this case the last 4 way and 3 way switches are within the old construction area of the building and are hard to get to.
- All I have coming from the old construction is a single 12/3 cable.
Thanks for your assistance.
This electrical wiring question came from: Ramon, a Homeowner from Gilroy, CA.
Additional Comments: Like the site. It has provided much guidance on my home addition.
Thanks for your electrical wiring question Ramon.
How to Wire a 4-Way Switch Light for Light Fixtures
- Unfortunately you would have to connect the new fixtures to the existing light fixtures.
- The 3-wire that runs between does not have a neutral wire, and besides, you would not have the correct switching sequence as the final common to the light fixtures from the end 3-way switch.
- Sorry for the bad news Ramon, just bring your helper or apprentice on the job and get him in the attic and put him to work pulling in that wire.
More about Wiring 4-Way Light Switches
4 Way Switch Wiring
4 Way Switch Wiring
Fully explained 4 way switch diagrams. 4-way switches are a convenient way to operate lighting fixtures from three or more locations. The electrical wiring adds additional wiring to the same principles of 3-way switching.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about 4-Way Switch, Lighting and Home Electrical Wiring:|
|« Previous||Next »|
|Installing Cadet Baseboard Electric Heaters||Wiring a Smoke Detector in a Basement|