Occupancy Sensors 3-Way and 4-Way Switches
How do I wire a motion a sensor to control lights? How to Wire 3-Way and 4-Way Occupancy Sensors to replace existing 3-way switches.
3-Way and 4-Way Occupancy Sensors for Indoor Motion Detector Applications
Electrical Question: How do I wire a motion a sensor to control lights?
I have a three family home unit and in the common stairwell I have a 3-way switch on the first floor, a 4 way switch on the second floor and a 3 way switch on the 3rd floor which are all controlling the common stairway lighting. My question is how do I install a motion sensor so all the lights will go on when my tenants leave their apt at night? Can you please help?
This electrical wiring question came from: Craig, a Homeowner from Bristo, Connecticut.
Thanks for your electrical wiring question Craig.
How to Wire a Occupancy Sensor Light Switch
Application: 3Way Light Switches.
Skill Level: Intermediate to Advanced – Best installed by a Licensed Electrician.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester.
Estimated Time: Depends on personal level experience and ability to work with tools.
Precaution: Identify the lighting circuit, turn it OFF and Tag it with a Note before working with the wiring.
Notice: Installing additional 3-way switch wiring should be done according to local and national electrical codes with a permit and be inspected.
Materials: Make sure replacement 3-way light switches have the same amperage and voltage rating as the original three way light switch, and is the switch is fully compatible with the electrical circuit, the light fixture and the type of light bulbs being used.
Wiring a 3Way and 4Way Occupancy Sensor
- Hi Craig, you have asked a great question. Consider installing 3 -way occupancy sensor switches that have a wide angle coverage and variable time delays.
- These 3-way occupancy sensor switches may replace the existing 3-way switches.
- Install a 4-way occupancy sensor to replace the existing 4-way switch.
- The sensing pattern should be adjusted as wide as possible and the time delay should be adjusted to provide enough time to travel the full distance of the stairway.
- This modification should be tested to make sure that the occupancy sensor pattern will accurately detect movement on the stairs.
- The sensing may be inhibited due to stairway design or obstacles in the area.
- If the motion detection of movement on the stairway does not activate the occupancy sensors then another solution should be considered.
3-Way and 4-Way Occupancy Sensor Light Switches
I have found for example, that Pass and Seymour has a multi-way Occupancy Sensor switch which you may consider for this application.
Click here for the PDF file: Multi-Way Occupancy Switches
More about Wiring Switches
Home Lighting Articles
- Home Lighting Articles covering recessed lighting, under cabinet lighting, lighting terminology and more.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Repair, Occupancy Sensor Switches and Home Electrical Wiring:|
|« Previous||Next »|
|Signs Of Electrical Troubles You Should Watch For||240 Volt Circuits and Switches|