Wiring a Photocell for an Outdoor Light Fixture
How to Wire a Photocell Control to an Outside Light Fixture: Matching a Photocell to an Outdoor Light Fixture, An Example for Wiring a 120Volt Photocell to Control the Light.
How to Wire a Photocell
Electrical Question #1: I would like control an outside light with a photo cell. How can this be done?
Wiring a 1000 Watt Outdoor Light
- The light is now wired for 240 volts and would like to switch it on and off with a photo cell. I have a photocell and was just wondering do you switch just one leg to shut it on and off and if that is the case why is a 240 volt photo cell needed? Each leg is 120 volts just looking for some understanding.
This electrical question came from: Joe in Michigan.
Electrical Question #2:
- I have a 3wire outside electric cord along with a AC DC Transformer (in. AC 100 240v, 125w) a photo cell (120v 4.2 amp 500w 7.1A ballast) with a red wire, white wire, and black wire. There are 4 12volt landscape spot lights with 1blue and 1Brown wire.
- I have the red wire from the photo cell to the brown wire of the spot light. The black wire from photocell to the black wire from the house circuit. All wires white to white, and the blue wire. The light will not turn off.
This electrical wiring question came from John in Florida.
Thank you for your electrical wiring questions.
Photocell Control for Outside Lights
Application: How to Wire a Photocell to Control a Outside Light Fixture.
Skill Level: Intermediate to Advanced. This electrical wiring project is best performed by a Licensed Electrical Contractor or a Certified Electrician.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester.
Estimated Time: Depends on personal level experience and ability to work with tools.
Precaution: Identify the light circuit, turn it OFF and Tag it with a Note before working with the timer switch wiring.
Notice: Installing additional fixture wiring should be done according to local and national electrical codes with a permit and be inspected.
Materials: Make sure the timer switch has the same amperage and voltage rating as the original switch, and is fully compatible with the electrical circuit, the light fixture and the type of light bulbs being used.
Wiring a Photocell to Control an Outside Light Fixture
Matching the Photocell to an Outdoor Light Fixture
- There are applications where a 240 volt load can be switched on and off using just one leg of power, but I would not advise it unless it is a built in control circuit of the equipment.
- The photocell to control your 1000 watt outdoor light fixture needs 240 volts to operate the photo cell, and because the 240 volt circuit does not have a neutral you cannot use a 120 volt photocell which does require a neutral.
- The solution is to get a photocell that matches the voltage configuration you have wired the outside light fixture for, and wire it according to the diagram.
- Photocells are available for most voltages and various watt or electrical circuit load requirements.
Photocell Basics: How a Photocell Operates
A photocell is basically an automatic switch that is controlled by sunlight during the daytime, and darkness during the night. The change from light to dark automatically activates the photocell to turn on the light fixtures that are wired to it.
Example of Wiring a 120 Volt Photocell
- The Electric Circuit and Line Wiring Connections
A typical photocell requires circuit wiring connection which would include the green ground wire, white neutral wire and the black circuit power wire.
- The Load Wiring Connection
The Load wiring of the photocell is typically where the black wire that leads to the light fixture is connected to the Red wire of the photocell.
- Remaining Light Fixture Wires
The white neutral wire and the ground wire of the light fixture connect to the white neutral wire and the ground wire of the photocell.
See More about Electrical Wiring for Outside Light Fixtures
Electric Wires for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
For more information about 220 Volt Wiring Diagram
220 Volt Wiring Diagram
Wiring 220 Volt Electrical Outlet
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how electrical outlets for the home are wired.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring, Photocell and Home Electrical Wiring:|
|« Previous||Next »|
|Installing a GFCI Outlet Without a Ground Wire Video||How to Wire Ceiling Fans and Switches|
I have a friend that wants to hook a photocell up in place of a time clock how is this done
A photo cell is wired just like a switch, only it needs a neutral. Photocells may also be used with a time clock if the lights should turn OFF at a special time, but accurately turn ON at dusk, very energy saving.
I bought a photocell for mounting outdoor. Could you please send me wringing diagram?
The voltage of the photocell as well as the make and model will need to be identified and the country where the photocell is to be installed for an accurate wiring diagram.
We purchased two outside wall lanterns to replace our current light fixtures. The new lights have built in photo cells, and our current wiring has a built in photo cell as well. Do we need to tape a wire off?
Great question Vickie,
In a case like this the photocells in each light fixture could be disconnected, however there really should not be a problem, except for a slight delay of the lights coming on after the main photocell turns on the circuit to the outside lights. If there is a problem then you could wire past each photocell and connect directly to the wires of the light sockets. Use electrical tape or wire connectors to cap off the disconnected wires.
I hope this helps you,
I would like to learn more about photo cell wiring diagrams 120 and 240 volts. Your website is very helpful.
I have two outdoor sconces that have individual photo cells that are small. Each photocell it has two wires. The fixtures are ten years old, and the photocells are hard to find. Could I use just a regular three wire photocell and not hook up the red wire? Thanks for your time.
A three wire photocell cannot be used to replace of a two wire photocell. However I have seen the two wire photocells at several popular hardware stores so I know they are available as a direct replacement.
Enjoy your light fixtures,