Wiring a Irrigation Pump and Control
How to Wire an Irrigation Pump Motor: Determining the Pump Motor Circuit Size, Electrical Codes and Wiring a Pump Motor.
Irrigation Pump Motor and Control
Electrical Question:I installed a new 1.5 HP irrigation pump and it throws the circuit breaker.
- I installed a new 1.5 HP irrigation pump, set the back voltage selector switch to 115 Volts also run the timer/relay off the same feed. the pump would run for a few minutes, then throws the 20amp breaker.
- After looking at the wire it was 14 gauge and the box is approx. 40’away so I ran some 10 gauge and replaced the breaker with a new 20amp and its doing the same thing.
- I understand running the timer off that line is incorrect but timer plugs in the wall with a 24 volt transformer would that be enough to throw the breaker?
Thanks for your help, I have done this in the past also have seen where the water softener installers have done the same and have never had this issue, Thanks for your help! Steve
This electrical wiring question came from: Steve located in Merritt Island, Florida.
Thanks for your electrical wiring question Steve.
How to Wire an Irrigation Pump Motor
Application: Wiring an Irrigation Pump Circuit.
Skill Level: Intermediate to Advanced, Best installed by a Licensed Electrical Contractor.
Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester, trenching equipment or shovels.
Estimated Time: Depends on personal level experience, ability to work with tools and install electrical circuit wiring.
Precaution: Identify the panel circuit, turn it OFF and Tag it with a Note before working with the wiring. Working in an electric panel is dangerous due to arc flash hazards and the possibility of electric shock.
Notice: Installing additional circuit wiring should be done according to local and national electrical codes with a permit and be inspected.
Wiring an Irrigation Pump Motor
- Determining the Pump Motor Circuit Size A typical 1 1/2 HP motor configured for 115 volts will require a 20 amp circuit. However check the specs on the motor nameplate for specific information. If a timer is being used to control the pump then the contacts of the timer must be rated for the voltage and amperage load of the motor. As stated in this question, it would be best if a control timer is wired as part of the pump circuit.
- Electrical Codes and Wiring a Pump Motor
- Code compliance for install a irrigation area pump motor is very important.
- Verify the circuit requirements for a 120volt 20amp or as specified by the pump motor installation manual.
- Electrical wiring should be sized according to the required circuit size.
- Protection for the electrical wiring should be provided. For example, installing underground electrical conduit at the required depth for the pump motor application.
- Contact the local building authority in your area of Florida about the codes specific to your project.
More about Electrical Wiring for a Pump Motor
Electrical Codes for Circuits
Related Questions about pump
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring, Pump Circuit and Home Electrical Wiring:|
|« Previous||Next »|
|Baseboard Heater Electric Circuit||How to Replace Electric Outlets|