Why Are There White Wires On My Switch?
Why White Wires are Sometimes Used for Light Switches: Wiring Light Switches with White Wires
Wiring Light Switches with White Wires
Electrical Question: I am changing out a ceiling fan and wall switch.
- When I pulled the existing switch the White wires (I assume they were neutral wires) were connected to switch.
- This made me nervous and I wanted to double check which wire was hot.
- So I tested the wires – Hot to Neutral 125v, Hot to Ground 35v, Neutral to Ground 30v.
- I opened every other box I could find on this circuit and they seem OK (I checked wire nuts, screws), tested one of them and got 125volt.
- I did not find the feed wire to my fan switch in the other boxes though, it’s a blue Romex and the only ones I found were white. Any suggestions? Is this dangerous?
- Attic access to this spot is very difficult and unbearably hot in Florida during the summer even at night (trust me I did it last Sunday night).
- The previous fan installed by a previous owner was still functioning after about 20 years.
Background: Bill, a Handyman from South Florida.
Thanks for your electrical wiring question Bill.
Why White Wires are Sometimes Used for Light Switches
At times, we still find in some older homes that White Wires are used for wiring light switches, and the light switch wiring method is different, however we also find White Wires being used today for wiring light switches however the method is entirely different.
- Some older homes were wired where the Neutral was switched, not the hot, and thank goodness that is not the practice today.
- However many times an electrician will use a white wire as a switched leg, but when this practice is used the wire should be identified with black electrical tape.
- The 35 volt reading form hot to ground should be checked. This is sometimes an indication of a neutral feedback when one of the main power legs is lost on a 240 volt service, but this may also be an indication that the neutral wire is being switched, and you may find that when the switch is in the ON position this voltage reading will change to zero or 120 volts, factors within the circuit will affect this including the type of light bulbs that are used in the light fixture.
- This may or may not be the case with your situation, to know for sure you should have a qualified electrician perform a few tests that would reveal the condition.
More about Wiring Light Switches
Wiring a Light Switch – Diagram 1
Fully Explained Light Switch Wiring Diagrams. Detailed Electrical Wiring Diagrams and Pictures assist your Home Electrical Projects.
Electrical Circuit Wiring
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical, Troubleshooting and Home Electrical Wiring:|
|« Previous||Next »|
|How To Convert a 30 Amp 250 Volt Outlet to a 15 Amp 220 Volt Outlet||Cause of No Power to a Home Electrical Circuit|