Why Air Conditioners Trip Circuit Breakers
Air Conditioner Units and Tripping Circuit Breakers: The circuit that an air conditioner is connected to may be shared with other outlets so the circuit is becoming overloaded, here is how to solve this problem.
Air Conditioner Electric Circuit
Electrical Question: I live in an NYC apartment with two roommates and this apartment, though spacious, is really inconvenient. We have a window Air Conditioner (AC) set up in the living room but it only cools down that room and the kitchen, not the little hallway leading into our bedrooms.
- We all have portable AC units in our room for that, but whenever I try to turn on my portable AC, the window AC also goes off after a minute or so, we noticed that the circuit breaker keeps popping/tripping so we go back and reset it. However, only the window AC automatically turns back on, while my portable AC does not. If I try to turn it back on, it runs for a minute again and then shuts off, popping the circuit breaker switch again.
- My roommate’s portable AC is able to run at the same time as the window AC, and the other roommate’s portable AC is on a different circuit (fairly certain since she never seems to have problems with it shutting off), so right now I’m the only one without AC and it is sweltering in this NYC heat.
- The switch that keeps popping says it has 15 amps on it. The window AC is 11,000 BTU and my portable AC is 10,000. There’s a bunch of other 15 amps switches and 2 other longer/bigger looking switches that say 40 amps on them. Is it overloading on that one 15 amp circuit? Yesterday, I tried turning off the window AC to turn mine on, but it still tripped the circuit.
- However, tonight I turned my portable AC on with the window AC running and it is working. My roommate’s portable AC is off though so I think maybe that all three AC units can’t run at the same time?
- I contacted my landlord who said he would send his repairman over to look at it soon but he’s slow with these things so I don’t know how soon that will be. What exactly can be done in this situation, is it possible to somehow rewire the circuit so that one of our AC units can go onto a different circuit and everyone can have their AC units on?
This electrical question came from: Stacy, from New York, New York.
Thanks for your electrical wiring question Stacy.
Air Conditioner Tripping the Electrical Circuit
Portable Air Conditioner Units and Electrical Circuit Requirements
- As described in this question, the circuits that the air conditioners are connected to are shared circuits that are becoming overloaded which is causing them to trip off.
- This typically happens when a portable or window air conditioner is plugged into an outlet circuit that may be shared with other outlets, so the circuit can become overloaded and cause the circuit to trip off.
- A dedicated circuit should be installed for each window air conditioner which will prevent the room outlets from becoming overloaded.
See More about Home Electrical Wiring
Electrical Circuit Wiring
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Rewiring a Home
Rewiring a Home
Great ideas for home electrical rewiring that will add value to your home and bring it up to the current safety and energy efficient electrical codes.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Electric Well Pump Circuits||Switch Outlet Wiring for an Old House|