Understanding Sub-Panels and Neutral Wires
Is it true that an uninsulated neutral is not allowed to be used with the power feed cable for a sub-panel? Electrical Panels with Neutral Wires and Ground Wires.
Sub-Panels Require a 4-Wire Cable with an Insulated Neutral
Electrical Question: Is it true that an uninsulated neutral is not allowed to be used with the power feed cable for a sub-panel?
The main line coming into my home and my fathers home from the power company transformer to my main box is not insulated. There are 3 wires from the pole twisted 2 insulated and one that is not. So is this a Double Standard where the power company can do whatever they want?
This electrical question came from: Greg, a Homeowner from Durham, North Carolina.
Thanks for your electrical wiring question Greg.
Wiring a Sub Panel with an Insulated Neutral and Separate Ground
Application: Wiring a Sub Panel.
Skill Level: Intermediate to Advanced. This electrical wiring project is best performed by a Licensed Electrical Contractor, and is not recommended for Homeowners.
Tools Required: Electricians pouch of hand tools and the various power tools necessary for installing the sub-panel.
Estimated Time: Depends on the type and size of the panel and available access to the project area.
Precaution: Any existing electrical wiring within the immediate area that may interfere with the installation of the sub panel should be identified and turned OFF and Tagged if necessary. Working in an electric panel is dangerous due to arc flash hazards and the possibility of electric shock.
Notice: Installing additional electrical wiring and a sub-panel should be done according to local and national electrical codes with a permit and be inspected.
Understanding Electrical Panels with Neutral Wires and Ground Wires
Greg, the panel that you are referring to is a Sub-Panel, not a Main Panel, and there is a Big Difference which I will explain with the following example:
- All single phase 240 volt Sub-Panels MUST have a 4-wire cable feed which must have a separate insulated neutral wire and a separate ground wire, which may be uninsulated.
- The neutral wire used with the Main Panel overhead service feed from the electrical utility company is most always un insulated as you and your father observed. If the Main Service feed was underground then the neutral wire would be required to be insulated.
- There is no Double Standard, and the power company cannot do whatever they want because they have electrical codes to follow as well. The only difference would be in some third world countries where they do not have established codes like we do here in the USA.
More about Wiring Electric Panels
- Sub-Panel Electrical Wiring for the Home
Electrical Sub-Panel wiring considerations for the home complete with pictures.
- Careful planning for your Sub-Panel with immediate and future load considerations will help you understand how to size your Sub-Panel.
- This information will help as you consider a Sub-Panel and its size.
- House Wiring Circuits and Circuit Breakers
- This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
- Electrical Wire for the Home
- Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring, Panel Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Upgrading Knob and Tube Electrical Wiring||Basic Ceiling Fan Remote Control Problems|