Question – Troubleshooting a Dryer Plug
What causes a 240 volt outlet to give only 120 volts?
I have a 220 line for my dryer. Sometimes it fails. When it failed I tested the outlet. I got 125 from the left leg and 25 from the right. I reset all the breakers and reread and it read correctly at 125 each leg. I don’t know how to check the breaker to tell you its reading, but do you have any idea what would cause this intermittent problem?
From what you are explaining, you are experiencing a problem with the circuit breaker where one of the two connections to the panel buss has become corroded and is arcing. This will cause an intermittent connection until it finally arcs so bad that this connection becomes totally lost. I would strongly advise you to get a qualified electrician to correct this situation right away as it could lead to much more severe problems in the panel. The severity of the problem depends upon the brand of the panel and the style of breaker. Zinsco Panels are popular for this problem as well as other brands especially when a twin breaker is used. Twin breakers are thinner and have less contact surface with the buss which can contribute to over-heating and create arcing while the circuit is being used. Many times a new full size breaker can be installed in a different position in the panel where the buss has not been damaged and your circuit will be restored.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Dryer Outlet Questions and Home Electrical Wiring:|
|« Previous||Next »|
|Question – 200 Amp Main Circuit Breaker Tripping – Part 1||Question – Steps to Take to Lower Your Electric Bill|