# The Shocking Truth About Neutral Wires

 Why am I getting 120 volts from a neutral wire? Why There May be Voltage on a Neutral Wire. Some of the worst shocks I have ever received while working on live circuits was from neutral wires, here is why and How You Can Prevent Electrical Shock from a Neutral Wire.

## Hooking Up a Generator to the House Panel Using a Circuit Breaker Interlock Kit for Backup Power

NOTE: A List of All my Helpful Videos
Will Display at the End of This Video

with my online Video Course:
Basic Home Electrical Wiring by Example

120 Volts on a Neutral Wire
Electrical Question: Why am I getting 120 volts from a neutral wire?

• Is it normal to have 120 volts from a neutral wire?

This electrical wiring question came from: Dan, a Homeowner from Kailua, Hawaii.

Thanks for your electrical wiring question Dan.
Wow – This is a Loaded Question, so here goes!

## Why There May be Voltage on a Neutral Wire

• 120 Volts on a Neutral Wire
NOTE: Even though this question lacks a lot of information, (such as what are you testing and how you are testing it), however I will explain a few situations where you are sure to get a 120 volt reading on a neutral wire. Lets say you have an incandescent light bulb in a fixture.
• Light Bulb Circuit Example
The light bulb itself has a small coil of wire which glows bright when power is applied. One side of this coil of wire connects to a hot wire, the other side connects to the neutral wire. When power is applied it runs through the coil, lights it up, and the power flows to the neutral and back to the bonded ground system of the electrical panel. This completes the circuit.
• Disconnected Neutral Wire
Now I disconnect the neutral wire anywhere after the connection to the light bulb, and using a voltage tester connect one lead to the disconnected neutral wire from the light fixture and the other tester lead to the neutral wire that continues to the electrical panel. If the power was turned on to the light bulb the light bulb would not light up, however I will get a 120 volt reading on my tester because the tester has been placed in the middle of the neutral wire which runs back to the electrical panel and my tester is in fact completing the circuit in a very limited way due to the internal circuitry of the type of tester being used.
• The Flow of Electricity
The amount of electricity flowing through the tester depends on the type of tester being used. If the tester is a digital type then no current would flow through the tester, but if the tester was an inductive type that has a coil of wire then there will be a flow of electrical current that goes through the tester, yet in each instance the amount of electricity would depend on the resistance of the tested circuitry.

### Now for the Shocking Truth about Neutral Wires

• Shocks from a Neutral Wire
If you understand the explanation above then you should realize just how easy it is to get an electrical shock from a neutral wire, in fact some of the worst shocks I have ever received while working on live circuits was from neutral wires. This happens when the circuit is completed either by the connection of the neutral wire path back to the ground system or any other connection that is grounded including a person.
• Resistance and the Circuit Path
The shock can be lethal because of the amount of electricity that can flow through the person due to the connected load and their resistance or lack of resistance a person may have to a ground source. The danger takes place if a person gets into the awkward position of being right in the middle of the neutral path to ground, and it hurts like the dickens, can knock you on your rear end, throw you across the room, cause you to yell, or any manner of uncomfortable results including possible lethal results including death!
• Turn Off the Circuit
This is why it is extremely important to always positively identify and turn off any electrical circuit that you may be working on, even if you are working on just the the neutral wires, because if you become grounded or caught in the middle, your sure to get shocked, and this is called Not Fun!

Using electrical testers

Electrical Safety and Voltage Testers
When working on home electrical wiring, quality voltage testers can play an important part in electrical safety. Electrical testers enable you to identify electrical circuits and help prevent the possibility of accidental electrical shock.

Electrical Troubleshooting

Troubleshooting Electrical Wiring
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.

The following may also be helpful for you:

## Dave's Guide to Home Electrical Wiring:

» You Can Avoid Costly Mistakes! «

Wire It Right with the help of my Illustrated Wiring Book
Great for any Home Wiring Project.

## Complete Guide to Home Electrical Wiring

Perfect for Homeowners, Students,
Handyman, Handy Women, and Electricians
Includes:
Wiring GFCI Outlets
Wiring Home Electric Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring Light Switches
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshoot and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
NEC Codes for Home Electrical Wiring
....and much more.

## Learn more about Home Electrical Wiring with my Online Video Course:Basic Home Electrical Wiring by Example

Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.

## The Safest Way to Test Electrical Devices and Identify Electric Wires!

The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.

## The Quickest Way to Check for Faulty Electrical Wiring!

The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.

## Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!

The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..

The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.

 More articles about Electrical, Testing and Home Electrical Wiring: « Previous Next » Circuit Breakers and Electrical Wiring Safety Replacing a Thermostat

5 Responses to “The Shocking Truth About Neutral Wires”
1. Lucy Evans says:

Great answer to a question more common than some people think!
We’re often getting similar questions from customers. We’ll point them to your detailed explanation ðŸ™‚

2. Russell says:

The home I bought was built in 1979. There are several flourescent light fixtures in the ceiling and none of them are working very well. Rather than buying lights, and ballasts, plus time involved to get them working correctly, I decided to replace the old fixtures (2 x 8′ lamps) with new T5 High Output Heavy Duty Strip ( 4 lamp T5HO) as I work in the garage a lot. I am 57, so the added light would be a welcome site.
Problem: When I removed one of the old fixtures, I discovered the wiring supplied was 14-2 romex (white/black/ground) and the new fixture is set up for 14-3 (white/black/red/ground). Is it possible to use the existing wiring or must new wiring be run?

3. Dave Rongey says:

Hi Russell,
I’d like to know a little more about the lights you want to install because if they are 120 volts then the power source should be the same as before. As for the original fluorescent light fixtures, make sure the ground wire is authentic and functional and bonded to the metal housing of the light fixture otherwise the lamps may be sluggish to start especially in cold temperatures. I too am experiencing the same thing in my shop where I have older 4 foot fixtures, the old shop light style, and I am having a pill of a time with lamps, they just do not last, and with the new increase in the cost for replacement lamps I am rethinking how I might upgrade, so I too would love more info about the fixtures you are planning to install.
Dave

4. Forrest Brown says:

I’ve always found it more useful, particularly in 3-phase 4-wire situations if the “Neutral” was referred to as a grounded conductor. If you consider it as a conductor, just like the “hot” wire, you’ll treat it with more understanding and respect.

5. Dave Rongey says:

Hi Forrest,
You are absolutely correct – I totally agree!