The Hot Tub Wiring Is Too Short Can I Install A Splice?
Yes – the wiring may be spliced in an approved junction box with a cover using appropriate wire connectors and bonding the ground to the junction box. The wiring from the junction box to the new location must be…
Electrical Question from Diana about Moving A Hot Tub Electrical Circuit
Background: Diana, a Homeowner from Burleson, TX
[ad#block]Question: I would like to move my hot tub and the electrical wires won’t reach the new location, can the wires be spliced to accommodate the move?
Thanks for your electrical question Diana. Yes – the wiring may be spliced in an approved junction box with a cover using appropriate wire connectors and bonding the ground to the junction box. The wiring from the junction box to the new location must be protected and the new hot tub service disconnect must be installed within sight of hot tub. More detailed information can be found here in this website. Just click the Hot Tub Wiring link below.
The Following links will assist you with your electrical question:
Hot Tub Wiring
For more information about Other Electrical Issue
Home Electrical Wiring
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Videos
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
The following may also be helpful for you:
Electrical Wiring Video #2
Home Electrical Wiring Videos about this Topic and More
Dave's Companion Guide to Home Electrical Wiring:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about Electrical, Hot Tub and Home Electrical Wiring:|
|« Previous||Next »|
|My Outlets Are Dead – Should I Replace The GFCI?||Why Does My Air Conditioning Circuit Keep Tripping?|