Is there a Dimmer Switch Rated for CU/AL Type Wire?
We have a three way switch in the dining room and would like to put a dimmer in but cannot find any dimmers that are CU/AL approved.
Electrical Question from Ryan about Light Switch Wiring
Received from Ryan a Homeowner in Nashua, NH
Question: I have a house that was built in 1968 and has Aluminum wiring. All of the switches and outlets are approved CU/AL rated. We have a three way switch in the dining room and would like to put a dimmer in but cannot find any dimmers that are CU/AL approved. First is this even possible? Second do they make such a switch? If yes where would I get one?
Additional Comments: Looks like a good website.
Thanks for your electrical question.
Hi Ryan – You will not find a dimmer switch rated for CU/AL Wire because most all dimmer switches come pre-wiredÂ with copper wire leads.Â You may connect the aluminum wire to the copper leads of the dimmer switch as long as you use a wire connector that is rated for CU/AL type wire connections.
The Following links will assist you with your electrical question:
For more information about Light Switch Wiring
Light Switch Wiring
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Pictures
Home Electrical Projects
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wiring!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester, [amazon.com], I use for the detection of Standard Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
|« My Florescent Light Fixtures are Not Working||Can I run Another Switch Off of the Existing Switch to Control the Ceiling Fan? »|