Installing an Outdoor GFCI Receptacle
Weatherproof GFCI Outlet Box: I am installing a GFCI receptacle on the outside of my home, the receptacle box cannot be recessed.
Electrical Wiring for a GFCI
Electrical Question: I am installing a GFCI receptacle on the outside of my home. The house is solid stone so the receptacle box cannot be recessed into the home. Is there a complete weatherproof GFCI box to house the GFCI receptacle made to surface mount on the wall?
Also with this the wire will be coming from out the corner of a basement window exposed for about 6-12″ to the GFCI receptacle. Since it will be exposed, can I still use NM Romex wire (14-2 for a 20 amp) with a metal conduit to protect the wire?
Background: Michael, a Homeowner from Philadelphia, PA
Thanks for your electrical question Michael.
Weatherproof GFCI Outlet Box
- There are single gang weather proof boxes that can be anchored to the stone wall using a masonry drill bit and plastic anchor.
- Conduit either consisting of PVC or EMT can be used to protect the wiring having a male connector and insulated plastic bushing placed on the open end which would protect the Type-NM cable that is installed.
- The Romex wire sheath should be removed from the portion of wire that is just past the entry of the conduit.
- The GFI receptacle and weatherproof cover will finish off the project along with installing conduit straps to anchor the conduit.
The Following links will assist you with your electrical question:
For more information about GFCI Wiring
GFCI Outlet Wiring
This link is helpful as a Homeowner
Make sure not to miss these Resources for: Other
Home Electrical Wiring Resources
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about GFI-GFCI and Home Electrical Wiring:|
|« Previous||Next »|
|Electrical Wire Connections for Ceiling Fans||Why Summer Heat May Cause Problems with Electrical Circuits|