Installing a programmable timer for an existing lighting system
If the new timer is to take the place of the existing system then you either need to identify that system and….
Electrical Question about installing a new programmable timer for a lighting system
Background:Â an Electrician from Rockford Illinois
Question: Trying to add a programmable timer to an existing lighting system. Upgraded to HWCFL, went from 24,115 watts to 5,300 watts. Shut power off at breakers, probed and power is still present. The contactors are in use with the existing system. Any ideas, do I shut off at the main relay panel?
Thanks for your electrical question. There is a lot of unknown information here, but if the new timer is to take the place of the existing system then you either need to identify that system and separate out the area you want to have controlled by your new timer or just remove the control wiring to the existing lighting contactor and replace it with your control wiring. You will need to check the control voltage and the existing relay voltage and coil load etc. to make sure you stay within the limits of the new timer control circuit. If you find that you are outside of the limitations of the timer control circuit then install an additional control circuit and use relays to accomplish the control process. The drop in wattage for the HWCFL is very nice. The client will have a nice energy savings.
The Following links will assist you with your electrical question:
For more information about Circuit Breaker
This link is helpful as a Electrician
Electrical Code Articles
Make sure not to miss these Resources for: Wiring Diagrams
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wiring!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester, [amazon.com], I use for the detection of Standard Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
|« How do I use existing electrical wiring for new deck lights?||How to connect breaker switches from the main electrical supply? »|