Installing a Combination Switch Outlet
How Can I install a Combo Switch and Outlet? Wiring a Combination Switch, Combo 3Way Switch Wiring, Switches and White Wires.
Wiring a Combination Switch Outlet
Electrical Question:How Can I install a Combo Switch and Outlet?
- I have a new Leviton Decora 5645-A combination 3-way switch and grounding receptacle that I want to install at the end of the line.
- One light is located in the middle and the power is coming into the 3-way switch at beginning of line.
- A 3 wire cable is installed between the twp three way switches and a light, 2 wire power in.
- How do I get continues power to the receptacle at the end of the line and still have 3-way switch?
This electrical wiring question came from: Dan, from Rochester, New York.
Thanks for your electrical wiring question Dan.
How to Wire a Leviton Combination Switch Outlet
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrician.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and install electrical circuit wiring.
Precaution: Identify the outlet circuit, turn it OFF and Tag it with a Note before working with the wiring.
- Wiring a Combination Switch
A combination switch outlet may not be installed at the location where it is the end of the three way switch wiring because there is no neutral wire present.
- Combo 3Way Switch Wiring
The combination switch outlet may be installed at the beginning of the three way switch location where the hot, neutral and ground wires are available.
- Switches and White Wires
You must keep in mind that switching does not involve a neutral wire, and just because a White Wire is present and used for switching does not mean that the white wire is a neutral wire, but in fact is most likely a white wire that is being used to as a switched power leg.
More about Wiring Light Switches
Wiring a Light Switch – Diagram 1
Fully Explained Light Switch Wiring Diagrams. Detailed Electrical Wiring Diagrams and Pictures assist your Home Electrical Projects.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wiring!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester, [amazon.com], I use for the detection of Standard Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
|« Causes of Lost Power to Outlets||Wiring Connections When Replacing an Oven »|