How to Install Wire for an Outbuilding
Installing Electric Wiring for an Outbuilding: How to Size and Calculate an Electric Panel for an Outbuilding, Online Electrical Load Calculator and Voltage Drop Calculator.
Electric Wiring for an Outbuilding
Electrical Question #1 I want to run a wire from my cottage out to a 9 x 12 outbuilding with a bedroom.
I intend on having probably 4 plugs, one outdoor light, and a ceiling fan and light. I would like to run a 1500 watt space heater (approximate size) from one of the plugs periodically. The main electrical line needs to run about 100 yards out from the cottage and the main electric service panel. How many amps would I need on that circuit and do I need to run thicker wire to run that far?
This home electrical wiring question came from John in Canada.
Electrical Question #2
- What gauge wire would I have to install from the main service to an outside building which is about 175 feet using a 50 amp breaker? The service will be underground. there will be a 110 volt air compressor, some lights, saws, and drills.
This electrical wiring question came from Johnny, a Homeowner in Kinder, Louisiana.
Thanks for your electric wiring questions.
John, the electrical circuits for an outbuilding must be carefully planned out so all of the wiring will be correctly identified and installed to make your outbuilding project is safe and according to code. This information will help you prepare for your outbuilding project.
Preparations for Wiring an Outbuilding
- Application: Outbuilding Electric Wiring.
- Skill Level: Intermediate to Advanced – Best installed by a Licensed Electrical
- Contractor or a Certified Electrician. This is Not Recommended for Homeowners.
- Tools Required: Electricians Tools including pouch of hand tools and the various power tools necessary for installing the sub-panel.
- Estimated Time: Depends on the type and size of the panel and available access to the project area, and trenching requirements for underground electrical wiring.
- Precaution: Any existing electrical wiring within the immediate area that may interfere with the installation should be identified and turned OFF and Tagged if necessary. Working in an electric panel is dangerous due to arc flash hazards and the possibility of electric shock.
- Notice: Installing additional electrical wiring should be done through the local building authority, installed according to applicable local and national electrical codes, with a permit, and have the required inspections.
How to Size an Electric Panel for an Outbuilding
- List all of the known electrical devices that will be used in the outbuilding.
- Add up all of the know electrical load information and add at least 25%.
- If high wattage electrical devices will be used such as motors or electric heating devices then additional factoring will be required based upon the area and specific circuit size.
- If electrical equipment will be used that requires a dedicated circuit for equipment such as laundry equipment or a well pump then more factoring will be required based on the length of wire that will be required.
- Add up how many circuits will be required for all of the electrical loads that have been identified.
- Depending on the size of larger outbuildings where multiple circuits will be installed then an electrical sub panel may be required.
- The outbuilding may require a sub panel with a main breaker and a dedicated ground system which will depend on the feeder cables that will be installed for the specific project.
- The outbuilding circuit size can only be determined when the total connected load has been identified and adjusted as required.
- Select the type of wire that will be installed for the outbuilding circuit, such as direct burial cable, or wiring that will be in conduit.
- Determine if the main feeder wire for the outbuilding will be copper or aluminum.
- NOTE: Aluminum wire may not be used for smaller gauges and is restricted in some areas.
IMPORTANT: If the electrical circuits for the outbuilding have not been well planned and installed correctly using the right methods and materials then the circuit will be vulnerable to breakdown and damage.
More about Electrical Wiring for a Outbuilding
- Determining the size of a Panel using a Electrical Load Calculator
- Sizing Wire for a Panel with a Voltage Drop Calculator
Electrical Codes for Home Wiring
- Electrical Code Directory covering several topics relating to home electrical wiring projects.
- Guide to Home Electrical Wire
Electrical Wire for the Home
- Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
- Wiring Ceiling Fans
How to Install Ceiling Fans
- Take the mystery out of ceiling fan wiring. Ceiling Fans are a great way to lower your energy bill and brighten up one of your favorite rooms.
- Electrical Circuit Wiring
- Common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
- How to Install Bedroom Electrical Wiring
Bedroom Electrical Wiring Requirements
- Fully Explained Photos and Wiring Diagrams for Bedroom Electrical Wiring with Code Requirements for most new or remodel projects.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wiring!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester, [amazon.com], I use for the detection of Standard Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
|« Adding Circuits to a Sub-Panel||Why An Electric Furnace May Cause Flickering Lights »|