How to Fix a Tripping GFI Outlet For a Refrigerator or Freezer
How Can I Fix a Tripping GFCI Outlet for a Refrigerator? Solve the Problem of a Tripping GFCI Refer or Freezer Outlet.
Problem with GFI Outlet for Refrigerator or Freezer
Electrical Question #1: How Can I Fix a Tripping GFCI Outlet for a Refrigerator?
- I have a refrigerator that is tripping the GFI outlet.
- The refrigerator has been plugged in this GFI for 2 years in the garage.
- Can I just replace the GFI outlet with an regular outlet?
This electrical wiring question came from: Joe, from Oxford, Florida.
Electrical Question #2: My refrigerator trips the garage GFI, should I replace the GFI?
- I have a three car garage, two overhead doors one double, one singe. I put a side by side refrigerator in the garage, and the GFI trips. The panel outside has a 15A breaker. Should I replace the 15A GFI with a 20A GFI?
This electrical wiring question came from Forrest, a Homeowner in Dacono, Colorado.
Thank You for your Electrical Questions.
How to Fix a Tripping GFI for a Refrigerator or Freezer
Application: Rewiring a GFCI Outlet Circuit.
Skill Level: Intermediate to Advanced, best if wired by a licensed electrician.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and the GFI outlet circuit that will be rewired.
Precaution: Identify the GFI outlet circuit, turn it OFF and Tag it with a Note before working with the wiring.
Notice: Installing additional GFCI Outlet wiring should be done according to local and national electrical codes with a permit and be inspected.
Solve the Problem of a Tripping GFCI Refer or Freezer Outlet
- Refrigerators and Freezers just don’t get along well with GFI Outlets, and the fact is they are not required to be protected by GFCI if they are on a circuit all by themselves and the circuit is not shared with other outlets in the garage or similar area.
- Because the refrigerator has worked fine with a GFI before, then my first recommendation is to replace the existing GFI outlet with a new one and see if that solves the problem, because just like an old electrician, GFI outlets can get old and tired and plum worn out.
- The problem is that most garages do no have a dedicated circuit and receptacle just for the refrigerator, but there is a way to solve this problem, however it will take a little rewiring and maybe one or more GFI Outlets to make this work.
- The point is to still have all the other outlets protected by GFI but not the refrigerator or freezer, so the outlet circuit that will need to be identified where it will be known where the power source enters the circuit, where the refrigerator or freezer outlet is in relationship to the other outlets and any additional outlets may be after the refrigerator or freezer.
- If there are any outlets before the refrigerator then they need to be wired as single protected GFI outlet and not wired with a Feed Through configuration.
- For outlets that are after the refrigerator they can be wired with a GFI outlet that is configured to provide Feed-Through protection to all of the following outlets. The links below will take you to a complete series of photos showing how to wire GFI outlets with the Single and Feed-Through methods.
More about Wiring GFI and GFCI Outlets
Wiring Electrical Outlets for the Home
- Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
- Wiring GFI Outlets
- GFCI and GFI Wiring Diagrams
- The features and benefits of GFCI outlets and receptacles will give you a clear understanding of the importance why these safety devices are required by code to help protect you and your family against accidental electrical shock hazards.
- GFCI Wiring
- This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
Garage Electrical Wiring
- Fully Explained Photos and Wiring Diagrams for Garage Electrical Wiring with Code Requirements for most new or remodel projects.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about GFCI, GFCI Outlet Questions and Home Electrical Wiring:|
|« Previous||Next »|
|Possible Causes for an Outlet Circuit not to Function||Causes of Lost Power to Outlets|