How Many Wires in a Receptacle Outlet Box
How to Install Wiring into an Outlet Box: Box Fill Calculation for Electrical Outlet Box. Guide for Installing electrical wires into an outlet box.
Electrical Wires in a Outlet Box
Electrical Question: How do I install electrical wires into an outlet?
- I have plastic Carlon blue shallow old work boxes that are labeled as having 17 cubic inches. I am hoping to use these boxes in shallow walls in my kitchen which has 2×3 framing.
- Do the poke through tabs that pinch the wires in the box count as internal clamps that need to be accounted for in doing box fill calculations? They are a molded part of the box and pinch the wire in place.
- The box says I can get seven 12 gauge box fill conductors in the box.
- With a cable going in the box and one going out to another receptacle, I have four conductors.
- Each receptacle counts two conductors.
- The ground wires count as one.
- That gives me seven conductors in the box fill calculations and at 12 gauge I am under 17 cubic inches.
- If those little pinching tabs count as internal clamps, however, that puts me at 8 conductors and over the box fill limit for the box.
- So to sum up, do those pinching tabs needed to be counted in these boxes? Using this box with 17 cubic inches can I get two 12 gauge cables and a receptacle in and not violate box fill?
This electrical wiring question came from Mike, in west Chester, Pennsylvania.
See more about Home Wiring for Pennsylvania
Thanks for your electrical wiring question Mike.
How to Install Wiring into an Outlet Box
Application: Electrical Wiring for Receptacle Outlets.
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrician.
Tools Required: Electricians Pouch of Hand Tools for Rough-In Wiring, Electric Drill and Auger Bits and Extension Cord.
Estimated Time: Depends on the extent of the bathroom remodel project, the type of construction and available access to the project area.
Precaution: Any existing wiring in the immediate area that may interfere with the installation of new construction materials should be identified, turned OFF and Tagged.
Notice: Modifying existing wiring or installing additional bathroom electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
Box Fill Calculation for Electrical Outlet Box
Example: Guide for Installing Electrical Wires into an Outlet Box.
- According to NEC 314.16(B) there is no allowance for small fittings, and because these clamps are an internal part of the box then they are included into the calculation as provided by the box manufacturer.
- If the box states the allowed number of conductors per wire gauge, then the box is already taking into account the built in clamps.
- With this 17 cubic inch box and the information that is supplied with the box you should have enough space for your wires and a receptacle for each box.
More about Junction Box Electrical Wiring
Electrical Code for Electrical Box Fill Capacity
- One of the mistakes often made is over loading an wire electrical box with too many wires.
- This will cause switches and outlets to not fit correctly and could even cause wires to become damaged.
- This information will help you plan your electrical box size properly.
Junction Boxes for Electrical Repairs and Home Remodel Projects
Electrical Junction Boxes for Home Wiring
- Understanding electrical junction boxes and what they are used for. Home electrical wiring is the process of installing electrical wire to a location that will serve electrical devices or an appliance. One very important component is the box where the wire will be installed.
- The type and size of the home wiring electrical boxes will depend upon the circuit size, application and its location.
Wire for Electrical Repairs and Home Remodel Projects
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|How to Test Receptacle Outlet Circuits||Methods for Splicing Electrical Wires|