How Do I Install Electrical Wiring For A Pond Pump?
Larry in Milford, Ohio asks: How to Wire a pond pump back to house to junction box on outside foundation through wall and…
Electrical Question from Larry about Wiring A Pond Pump
Background: Larry, a Homeowner from Milford, OH USA
Question: Wiring a pond pump back to house to junction box on outside foundation through wall and wire into a line with a switch and continue out to rest of receptacles in this line. Diagram?
Thanks for your electrical question Larry. From the house junction box I would recommend installing a half or three quarter inch PVC conduit in a trench to the required depth of 18 inches which would end at the desired location at the pond. The larger three quarter inch size is not that much more expensive and will allow you to pull the wire through much more easily. An alternative is to install a Direct Burial Type UF Cable at a depth of 24 inches which would be protected with PVC at each end of the bottom of the trench, up to the junction box locations where the cable emerges. The junction boxes and associated materials must be rated NEMA 3-R for outdoor use. The circuit must be GFCI protected and weather proof covers which can accommodate the pump cord being plugged in and covered as well. The wire gauge must be sized the same as the wire at the house. This project should be installed with a permit and inspection. Please see the Electrical Codes link below for more information.
The Following links will assist you with your electrical question:
For more information about Electrical Wiring
This link is helpful as a Homeowner
Make sure not to miss these Resources for: Wiring Diagrams
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|« What Are The Electrical Codes For Above Ground Pools?||How To Wire a GFCI and Outlet to a Light Switch »|