Grounding an Electrical Equipment Disconnect Switch
How to Bond The Ground: I Need to Place A Disconnect Between A Radial Saw And The Main Power Breaker.
Bonding The Ground to a Disconnect Switch
[ad#block] Electrical Question: I Need to Place A Disconnect Between A Radial Saw And The Main Power Breaker.
- The Voltage Is 220 Volt 3 Phase With A Ground.
- The Disconnect Box That I Have Is a 30 Amp Box With 3 Wire Lugs In And 3 Wire Lugs Out But No Lug For The Ground Wire.
My Question Is If I Wire Nut The Ground Wires Together Is This Ok To Do And Is It To Code?
This electrical wiring question came from: Gus, a Other from Cincinnati,Ohio
Thanks for your electrical wiring question Gus.
How to Bond The Ground
- The ground wires can be spliced together however the metal disconnect enclosure must have a ground bonded to it as well.
- This can be done using a pigtail wire from the splice or by mounting a short terminal strip to the disconnect switch using a threaded machine screw.
Based on your question Gus, the following specific links may be helpful to you:
Electrical Wiring Protection using Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Electrical Code Articles
Electrical Code Directory covering AFCI circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, electrical GFCI, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-code, smoke-detector,
You identified your project to be about Electrical Wiring, so you might find this information useful:
Home electrical wiring projects with pictures and wiring diagrams.
The following may also be helpful for you:
Electrical Wiring Video #2
Home Electrical Wiring Videos about this Topic and More
Learn more with my Home Electrical Video Course:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about Disconnect Switch and Home Electrical Wiring:|
|« Previous||Next »|
|What to do When the Panel Neutral Bar is Full||Installing Wiring for a Garage Panel|