Electrical Question from Sal in New York about Wiring 3Way Switches
There are three switches in a 3 gang box, do I need the 12/3 wire: Electrical Question from Sal in New York about Wiring 3-Way Switches.
Do You Need Electrical Help?
Guide to Residential Electrical Wiring
Sal in New York asks about Wiring 3-Way Switches
Question on wiring, there are three switches in a 3 gang box. The switches control a ceiling fan (bathroom), a shower light and the last switch a main bathroom light. The black wires are connected to the switches, the white are all connected, the ground are all connected. There is a black wire that connects to the top screw pig tailed to each switch. Then from this box a 12/3 wire goes to a GFI outlet that has black and red connected to one GFI screw and a white to another screw. In the three gang box the original switch the red and black (pigtail) are connected together. Is this a correct way? As I am relocating the GFI and main 3 gang box to a four gang box. The four gang box will have the three switches and a GFI outlet. Do I still need the 12/3 wire as I note how it is now connected?
This electrical wiring question came from Sal, a Handyman, in Stony Point, New York.
Hi Sal, Great Question!
Yes, the 12/3 wire that goes to the GFCI outlet should be wired the same way inside the new 4 gang box.
All of the wiring remains the same, only the wiring will be contained inside one 4 gang box, therefore make sure to carefully mark the wires to ensure the same connections as originally found, and make sure the size of the new 4 gang box will have the space for all the wires.
More about Electrical Wiring Three Way Switches
Electrical Switches: 3way switch review
Electrician Reviews the Most Common Types and Styles of Three Way Light Switches.
You Can Avoid Costly Mistakes!
Here's How to Do It:
Wire It Right with the help of my Illustrated Wiring Book
Great for any Home Wiring Project.
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electric Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring Light Switches
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
How to Troubleshoot and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
NEC Codes for Home Electrical Wiring
....and much more.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
Electrical Tips to Help You Wire it Right
The Safest Way to Test Electrical Devices and Identify Electric Wires!
The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!
The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets
Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency
Lights indicate if wiring is correct and indicator light chart is included
Tests standard 3-wire outlets
Light indicates if wiring is incorrect
Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!
The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.