Electrical Question about a Receptacle at the End of a Line
I have a receptacle at the end of a line with 1 set of wires coming into the wall box, that I want to make into a blank wall plate
Do You Need Electrical Help?
Guide to Residential Electrical Wiring
Electrical Question from Scott about a Receptacle at the End of a Line.
Received from Scott a Homeowner in Trappe, PA
Question: I have a receptacle at the end of a line (1 set of wires coming into the wall box), that I want to make into a blank wall plate (otherwise would need to put in a GFCI in a shallow box situation due to concrete wall). To do this, can I simply connect black to white by wire nut, and put a blank plate?
Additional Comments: cool site!
Thanks for your electrical question.
Hey Scott – If all you want to do is keep the wiring in this outlet box and place a blank cover over it then just place a wire nut on the end of each wire separately. Do not join the two wires together because that would create a direct short circuit and trip off the circuit breaker. If you need this outlet but need gfci protection then install a gfci at the location that feeds this outlet. You would be wiring the gfci using the Feed Through Method as described in the gfci area of the main website. Use the link below for complete information:
GFCI Wiring Diagram Feed Through Method
This article is about gfci wiring using the feed through method which will protect more than one outlet.
The Following links will assist you with your electrical question:
For more information about Circuit Wiring
This link is helpful as a Homeowner
Make sure not to miss these Resources for: Wiring Diagrams
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
You Can Avoid Costly Mistakes!
Here's How to Do It:
Wire It Right with the help of my Illustrated Wiring Book
Great for any Home Wiring Project.
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electric Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring Light Switches
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
How to Troubleshoot and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
NEC Codes for Home Electrical Wiring
....and much more.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
Electrical Tips to Help You Wire it Right
The Safest Way to Test Electrical Devices and Identify Electric Wires!
The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!
The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets
Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency
Lights indicate if wiring is correct and indicator light chart is included
Tests standard 3-wire outlets
Light indicates if wiring is incorrect
Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!
The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.