Electrical Question about a Portable Infrared Sauna
I’ve been building a portable infrared sauna. I know nothing about electrical work, but did my best to follow the instructions. When I plugged it in, there was a huge spark and popping – obviously, something is wrong.
Electrical Question from Steve about a Portable Infrared Sauna
Received from Steve a Homeowner in Toronto, Ontario, Canada
I’ve been building a portable infrared sauna. I know nothing about electrical work, but did my best to follow the instructions. When I plugged it in, there was a huge spark and popping – obviously, something is wrong. I’ve attached 4 photos. Can you tell me where I’ve gone wrong?
Thanks for your electrical question.
Steve – from the looks of the arcing that occurred at one of the plug prongs you have a direct short.
Steve, I’m sure the doctor has great intentions but this assembly isÂ a fire hazard and has a few terrible electrical code violations.
I would never use this device in my home or instruct others to assemble this for their own home use.
Here are a fewÂ problems I see with this design and from the information I see on the doctors website:
Mounting lamp sockets into a flammable wood board is a fire hazard.
The lamp sockets and wiring terminations are not mounted to or protected by an approved fixture box enclosure, therefore they are a fire hazard and they are open to human contact which could result in an electrical shock.
The wire is not anchored or supported.
This type of lamp wire is incorrect and may over heat at 1000 watts of load.
The entry of the lamp cord into the electrical switch box in not protected by an approved bushing or cord clamp.
The absence of a ground wire throughout the device.
The plastic pvc frame is unstable and could collapse causing the unit to come into human contact and cause severe burns and cause aÂ fire to any flammable materials that theÂ assembly may Â come into contact with.
The doctor mentions using a lamp guard but the proximity of the flammable fabric material may notÂ be adequate to prevent a fire.
Let me know what you discover, the cause should be very obvious.
I am not including the photos here or the doctors website because of the hazardous design of this unit. I may place the photos in another area of the website for review and discussion
The Following links will assist you with your electrical question:
For more information about Light Switch Wiring
Light Switch Wiring
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Pictures
Home Electrical Projects
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|« Electrical Question from Sankar about Sizing Cable for a MCCB||Electrical Question from Pamela about Replacing Old Light Switches »|