Electrical Outlets and GFCI Wiring
I am replacing a GFCI per the instructions and I am hooked up on the LINE side (Black (hot), white and ground….
Outlet Testing and GFCI Wiring
Question: I am replacing a GFCI per the instructions and I am hooked up on the LINE side (Black (hot), white and ground. At this point the receptacle is working fine. As soon as I hook up the LOAD side I cannot get the GFCI to reset and stay on. What say you about this, do I have a problem on the LOAD side wiring? This receptacle has been working in the past as the house is some 3 years old. The GFCI is in a storage room in the basement.
Thanks in advance for your insights,
This electrical question came from: Dan, a Homeowner from Warren, New Jersey.
See more about Home Wiring for New Jersey
Thanks for your electrical question Dan.
The Following links will assist you with your electrical question:
How to Install Basement Electrical Wiring
Basement Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Basement Electrical Wiring with Code Requirements for most new or remodel projects.
For more information about GFCI Wiring
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
This link is helpful as a Homeowner
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about GFCI Outlets and Home Electrical Wiring:|
|« Previous||Next »|
|Light Switch Wiring for Bathroom Exhaust Fan||Installing Garage Electrical Wiring|