Attic Wiring, Junction Boxes and Electrical Safety
How to Store Unused Electrical Wires: Is it safe to leave live wires capped in switch box covered by flat plate?
Electrical Safety and Unused Attic Wiring
Electrical Question: Is it safe to leave live wires capped in switch box covered by flat plate?
- Having disconnected a 3-wire wall switch to an attic-mounted whole house fan, is it safe to leave live wires capped in the switch box covered by flat plate?
- The wires don’t touch each other or the box; they are capped.
- Is it safe to leave the fan hard-wired to the attic junction box?
This electrical question came from: John, a Homeowner from Naperville, Illinois.
Thanks for your electrical question John.
How to Store Unused Electrical Wires
Application: Storing Electrical Wiring in a Junction Box.
Skill Level: Intermediate to Advanced – Best performed by a Certified Electrician or Electrical Contractor.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester.
Estimated Time: Depends on personal level experience and ability to work with tools.
Precaution: Identify the circuit, turn it OFF and Tag it with a Note before working with the wiring.
Important: Burnt or damaged wiring and circuit components should be replaced with new electrical materials of the same voltage and amperage rating.
Notice: Repairs or changes to Home Electrical Wiring should be done according to local and national electrical codes and installing new or replacement electrical parts or equipment may require to have a permit and be inspected.
What to do with Unused Electrical Wiring
- Placing a fold of electrical tape over the end of a unused wire is fine in a temporary situation, but not as a long term solution.
- It is best to screw a insulated wire connector over the end of the wires and cover the box with a blank plate as you have mentioned.
- I don’t know if there is a problem with the whole house fan, but as long as the power source will not be connected to it then you can leave the wiring in the attic junction box, cap off the wires, and place a blank cover the junction box as mentioned.
More about Unused Electrical Wiring
- Electrical Code for How Many Wires in Junction Boxes
- Electrical wire
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
- Junction boxes
Electrical Junction Boxes for Home Wiring
Understanding electrical junction boxes and what they are used for. Home electrical wiring is the process of installing electrical wire to a location that will serve electrical devices or an appliance. One very important component is the box where the wire will be installed. The type and size of the home wiring electrical boxes will depend upon the circuit size, application and its location.
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Attic Wiring, Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|The Key to Wiring Three Way Switches||Dimmer Switches and Fluorescent Light Fixtures|
Can you wire an attic and put the light bulb mounts (and bulbs) on the roof trusses (next to the roof)? Can you also run wire on the roof trusses? Having electricity running within 8 inches of the roof in an electrical storm, is that safe?
I am trying to figure out the code violation of having spliced electrical wiring in an attic put together with wire nuts. There is exposed wiring, and I have photos I can send. From my understanding, all splicing of electrical wiring has to be contained in a junction box. Is this the case to remain in code? This is for CA.
Here is an example of providing an approved electrical splice in a junction box: Electrical splices must be made inside an approved electrical junction box which is properly installed and fastened, the cables entering the junction box must be secured with the appropriate box connectors, the splices must be made using insulated electrical connectors, the junction box must have a cover installed, and the junction box must be in an accessible location.
I hope this helps you with your junction box project. Thank you for sharing your electrical question,