» Residential Electrical Wiring: Guide to Home Wiring
» Need Electrical Help? Ask the Electrician
Air Conditioner Size and Room Electrical Circuit
The NEC states that the total rating of a plug-connected room air conditioner, where lighting units or other appliances are also supplied, shall not exceed…
Electrical Code for Room Air Conditioners
[ad#block]Question: The NEC states that the total rating of a plug-connected room air conditioner, where lighting units or other appliances are also supplied, shall not exceed what percent of the branch-circuit rating.
Background: Eddie is a Student from Sacramento, California.
Thanks for your electrical question Eddie.
Where the branch-circuit supplies lighting outlets and general use receptacles, the total rating of a plug-connected room air conditioner cannot exceed 50 percent of the branch-circuit rating. An example would be that an air conditioner with a full-load current of 10 amperes or less may be installed on a 20-ampere branch circuit that supplies other loads, and the receptacle that supplies power to the air conditioner should be rated for 20-amperes.
The Following links will assist you with your electrical question:
For more information about Electrical Code
Home Electrical Code
Electrical Code Directory covering AFCI Circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, Electrical GFCI, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-codes and smoke-detectors.
This link is helpful as a Student
Electrical Code Articles
Make sure not to miss these Resources for: Other
Home Electrical Wiring Resources
The following may also be helpful for you:
Electrical Wiring Video #2
Home Electrical Wiring Videos about this Topic and More
Dave's Companion Guide to Home Electrical Wiring:
|More articles about Electrical and Home Electrical Wiring:|
|« Previous||Next »|
|Considerations When Grounding Electrical Equipment||Electrical Outlets and Light Switch Wiring|
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.