Air Conditioner Size and Room Electrical Circuit
The NEC states that the total rating of a plug-connected room air conditioner, where lighting units or other appliances are also supplied, shall not exceed…
Electrical Code for Room Air Conditioners
[ad#block]Question: The NEC states that the total rating of a plug-connected room air conditioner, where lighting units or other appliances are also supplied, shall not exceed what percent of the branch-circuit rating.
Background: Eddie is a Student from Sacramento, California.
Thanks for your electrical question Eddie.
Where the branch-circuit supplies lighting outlets and general use receptacles, the total rating of a plug-connected room air conditioner cannot exceed 50 percent of the branch-circuit rating. An example would be that an air conditioner with a full-load current of 10 amperes or less may be installed on a 20-ampere branch circuit that supplies other loads, and the receptacle that supplies power to the air conditioner should be rated for 20-amperes.
The Following links will assist you with your electrical question:
For more information about Electrical Code
Home Electrical Code
Electrical Code Directory covering AFCI Circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, Electrical GFCI, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-codes and smoke-detectors.
This link is helpful as a Student
Electrical Code Articles
Make sure not to miss these Resources for: Other
Home Electrical Wiring Resources
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical and Home Electrical Wiring:|
|« Previous||Next »|
|Considerations When Grounding Electrical Equipment||Electrical Outlets and Light Switch Wiring|