Adding New Lights to 3-Way Switches
Wiring Three Way Switches – When adding additional lighting to an existing three way switch configuration, the only place the additional lights may be wired to are at the existing light fixture or to the switch box where the existing light fixture is wired to.
How to Add Lights to a Three Way Switch
[ad#block]Electrical Question: I recently installed 4 three inch recessed halogen lights and I have them on a three-way switch my problem is that when i turn on the first three-way THE ONE WERE POWER INITIALLY COMES FROM all the lights come on but the other three-way does nothing.
I recently purchased your three-way booklet which was very helpful for a three-way I had in a stairway but for some reason I am not understanding whats up on multi-fixture three-ways
This electrical question came from: Jeff, a Electrician from Riverside , California.
See more about Home Wiring for California
Thanks for your electrical question Jeff.
Wiring Three Way Switches
Jeff, when adding additional lighting to an existing three way switch configuration, the only place the additional lights may be wired to are at the existing light fixture or to the switch box where the existing light fixture is wired to.
Additional lights cannot be wired to the last 3-way switch because there will not be a connection for the neutral wire.
The Following will assist you with Electrical Wiring for Light Fixtures and Switches
How To Install Recessed Lighting
This article is about recessed lighting for your home electrical improvements. Discover how recessed lighting can enhance the mood of any room in your home.
For more information about 3 Way Switch Diagram
3 Way Switch Diagram
3 Way Switch Diagram
In response to the requests for this information, I have developed a comprehensive,step-by-step guide designed to walk you through the identification and wiring of your 3-way switches.
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about 3-Way Switches, Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|How Is A Switched Wall Outlet Wired?||How To Control Outside Electrical Outlets|