# Electrical Relay Construction and Purpose - Part 1

 By Dave Rongey Summary: This section will cover how relays are constructed and operate due to the current flowing through the control coil and the mechanical reaction that takes place.

## Install a Generator and Transfer Switch Panel

### So Keep Watching So I Can Help You Wire it Right!

The content is explained through industrial controls but the principles can be easily adapted to residential wiring applications as well.

An electric current through a conductor will produce a magnetic field at right angles to the direction of electron flow. If that conductor is wrapped into a coil shape, the magnetic field produced will be oriented along the length of the coil.

The greater the current, the greater the strength of the magnetic field, all other factors being equal.

 Inductors react against changes in current because of the energy stored in this magnetic field. When we construct a transformer from two inductor coils around a common iron core, we use this field to transfer energy from one coil to the other. However, there are simpler and more direct uses for electromagnetic fields than the applications we've seen with inductors and transformers. The magnetic field produced by a coil of current-carrying wire can be used to exert a mechanical force on any magnetic object, just as we can use a permanent magnet to attract magnetic objects, except that this magnet (formed by the coil) can be turned on or off by switching the current on or off through the coil. If we place a magnetic object near such a coil for the purpose of making that object move when we energize the coil with electric current, we have what is called a solenoid. The movable magnetic object is called an armature, and most armatures can be moved with either direct current (DC) or alternating current (AC) energizing the coil. The polarity of the magnetic field is irrelevant for the purpose of attracting an iron armature. Solenoids can be used to electrically open door latches, open or shut valves, move robotic limbs, and even actuate electric switch mechanisms. However, if a solenoid is used to actuate a set of switch contacts, we have a device so useful it deserves its own name: the relay.

 Relays are extremely useful when we have a need to control a large amount of current and/or voltage with a small electrical signal. The relay coil which produces the magnetic field may only consume fractions of a watt of power, while the contacts closed or opened by that magnetic field may be able to conduct hundreds of times that amount of power to a load. In effect, a relay acts as a binary (on or off) amplifier.

 Just as with transistors, the relay's ability to control one electrical signal with another finds application in the construction of logic functions. This topic will be covered in greater detail in another lesson. For now, the relay's "amplifying" ability will be explored. In the above schematic, the relay's coil is energized by the low-voltage (12 VDC) source, while the single-pole, single-throw (SPST) contact interrupts the high-voltage (480 VAC) circuit. It is quite likely that the current required to energize the relay coil will be hundreds of times less than the current rating of the contact. Typical relay coil currents are well below 1 amp, while typical contact ratings for industrial relays are at least 10 amps. One relay coil/armature assembly may be used to actuate more than one set of contacts. Those contacts may be normally-open, normally-closed, or any combination of the two. As with switches, the "normal" state of a relay's contacts is that state when the coil is de-energized, just as you would find the relay sitting on a shelf, not connected to any circuit. Relay contacts may be open-air pads of metal alloy, mercury tubes, or even magnetic reeds, just as with other types of switches. The choice of contacts in a relay depends on the same factors which dictate contact choice in other types of switches. Open-air contacts are the best for high-current applications, but their tendency to corrode and spark may cause problems in some industrial environments. Mercury and reed contacts are sparkless and won't corrode, but they tend to be limited in current-carrying capacity. Shown here are three small relays (about two inches in height, each), installed on a panel as part of an electrical control system at a municipal water treatment plant: The relay units shown here are called "octal-base," because they plug into matching sockets, the electrical connections secured via eight metal pins on the relay bottom. The screw terminal connections you see in the photograph where wires connect to the relays are actually part of the socket assembly, into which each relay is plugged. This type of construction facilitates easy removal and replacement of the relay(s) in the event of failure.

 Aside from the ability to allow a relatively small electric signal to switch a relatively large electric signal, relays also offer electrical isolation between coil and contact circuits. This means that the coil circuit and contact circuit(s) are electrically insulated from one another. One circuit may be DC and the other AC (such as in the example circuit shown earlier), and/or they may be at completely different voltage levels, across the connections or from connections to ground.

 While relays are essentially binary devices, either being completely on or completely off, there are operating conditions where their state may be indeterminate, just as with semiconductor logic gates. In order for a relay to positively "pull in" the armature to actuate the contact(s), there must be a certain minimum amount of current through the coil. This minimum amount is called the pull-in current, and it is analogous to the minimum input voltage that a logic gate requires to guarantee a "high" state (typically 2 Volts for TTL, 3.5 Volts for CMOS). Once the armature is pulled closer to the coil's center, however, it takes less magnetic field flux (less coil current) to hold it there. Therefore, the coil current must drop below a value significantly lower than the pull-in current before the armature "drops out" to its spring-loaded position and the contacts resume their normal state. This current level is called the drop-out current, and it is analogous to the maximum input voltage that a logic gate input will allow to guarantee a "low" state (typically 0.8 Volts for TTL, 1.5 Volts for CMOS). The hysteresis, or difference between pull-in and drop-out currents, results in operation that is similar to a Schmitt trigger logic gate. Pull-in and drop-out currents (and voltages) vary widely from relay to relay, and are specified by the manufacturer. REVIEW: A solenoid is a device that produces mechanical motion from the energization of an electromagnet coil. The movable portion of a solenoid is called an armature. A relay is a solenoid set up to actuate switch contacts when its coil is energized. Pull-in current is the minimum amount of coil current needed to actuate a solenoid or relay from its "normal" (de-energized) position. Drop-out current is the maximum coil current below which an energized relay will return to its "normal" state.
» You Can Avoid Costly Mistakes! «

Here's How to Do It:
Wire It Right with the help of my Illustrated Wiring Book

Great for any Home Wiring Project.

## See How to Wire it Right!

Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students and Electricians
Includes:
Home Electrical Wiring - Upgrade Electrical Wiring
Wiring 120 Volt Circuits
Wiring 240 Volt Circuits
Wiring Multi-Wired Circuits
Wiring Methods for Installing Home Electrical Circuit Wiring
Electrical Codes for Home Electrical Wiring
Electrical Troubleshooting and Repairs
....and much more.

## The Safest Way to Test Electrical Devices and Identify Electric Wires!

The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.

## The Quickest Way to Check for Faulty Electrical Wiring!

The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.

## Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!

The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..

The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.

## Residential Electrical Parts and Accessories

Light Switches

120volt Outlets

Circuit Breakers

Electrician Tools

Voltage Testers

### More about Electrical Relay Construction and Purpose Part1

Multiple Motion Detectors for Light Fixtures
Can Two Motion Detectors be Used to Control Outdoor Flood Lights? How to Wire Multiple Motion Detectors for Outside Lighting.

Motion Sensor Controlled Landscape Lighting
How can I use a motion sensor to control my outdoor landscape lights? How to Use a Motion Sensor to Control Landscape Lighting, A Solution to Motion Controlled Landscape Lighting.

Sitemap
Ceiling Fans Airplane Ceiling Fan Airplane Ceiling Fan Ceiling Fan Direction Summer Ceiling Fan Direction Winter Ceiling Fan Wiring Diagram 1 Ceiling Fan Wiring Diagram 2 Ceiling Fan Wiring Questions and Answers Ceiling Fans Wiring – Part 1 Ceiling Fans Wiring – Part 2 Introduction to Ceiling Fan Remote Controls Outdoor Ceiling Fan 1 Outdoor […]

Electrical Relay Construction and Purpose Part1 - 764