Question – 200 Amp Main Circuit Breaker Tripping – Part 2
My 200 amp main electrical circuit breaker trips. Should I replace it?
Do You Need Electrical Help?
Guide to Residential Electrical Wiring
Thanks for your quick response on this holiday weekend – you are correct, both AC units are running on 240V and by default are load balanced – its been a long week.
The LRA on the 4-ton unit is 105 and the LRA on the 2-ton unit is 55. The 4-ton unit’s compressor outside shows a min. fuse rating of 29A and a max of 50A – I was surprised to see that the 30A breaker that the 4-ton unit is on has never tripped. IÂ thought I may have needed a new 200A main or maybe the terminals on it were loose. I guess if both units fire at the same time and my pool pump, well and other appliances are on at the same time I will have a potential problem.
As for the time delay relay, what manufacturer/rating would you recommend?Â I will alsoÂ look at moving some of the higher 120V circuits, but the time delay relay sounds like a real fix- thank you!
Attached is the info on a relay that should work for you – I will be adding this to the web site soon as well, in fact here is a link to some new pages that explains relays – pay special attention to the time delay relay section. [Click here]
200 Amp Main Circuit Breaker Tripping – Part 1
200 Amp Main Circuit Breaker Tripping – Part 3
You Can Avoid Costly Mistakes!
Here's How to Do It:
Wire It Right with the help of my Illustrated Wiring Book
Great for any Home Wiring Project.
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electric Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring Light Switches
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
How to Troubleshoot and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
NEC Codes for Home Electrical Wiring
....and much more.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
Electrical Tips to Help You Wire it Right
The Safest Way to Test Electrical Devices and Identify Electric Wires!
The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!
The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets
Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency
Lights indicate if wiring is correct and indicator light chart is included
Tests standard 3-wire outlets
Light indicates if wiring is incorrect
Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!
The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.