200 Amp Electrical Service Upgrade Riser
How an Electrical Service Entrance Pipe is Typically Used for a Panel Upgrade – The rigid conduit should be solid from the weather head down to the electric meter enclosure or main service panel.
Service Entrance Pipe for a Panel Upgrade
Electrical Question: I’m having my service upgraded to 200 amp my question is about connecting from the mast pipe coming through the roof to the new meter socket.
- The pipe coming through the roof is 2 in threaded and I would be would using a 2 in rigid coupling a 2 in watertight connector into that then EMT into another 2 in water tight connector to the meter socket hub, or do I have to buy a $40 stick of rigid conduit and a rigid connector or have it threaded to be code.
Background: Peter, a Handyman from Milwaukee WI
Thanks for your home electrical wiring question peter.
How an Electrical Service Entrance Pipe is Typically Used for a Panel Upgrade
Skill Level: Advanced – Licensed Electrical Contractor, Not Recommended for Homeowners.
Tools Required: Electricians pouch of hand tools and the various power tools necessary for the specific service upgrade.
Estimated Time: Depends on the type of panel and available access to the project area.
Precaution: This is an extensive project that should be performed by a Licensed Electrical Contractor.
Notice: Making changes to the Electrical Service Panel should be done with a permit and be inspected.
- Peter, you can check with your locals electrical codes, however the rigid conduit should be solid from the weather head down to the electric meter enclosure or main service panel.
- If a coupling is needed the it should be placed closest to the electric meter equipment which will allow for a solid length or rigid pipe to penetrate the roof for the service mast.
- Yes, rigid conduit is expensive however it offers the best protection.
- Some areas may allow IMC which is less expensive but it is still a solid conduit.
The Following resources will assist you with your electrical service upgrade:
Home Electric Panel
- House Wiring Circuits and Circuit Breakers
- This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
- Electrical Code for Conduit Fill
- Electrical Code
- Electrical Codes for Services
Wiring Electrical Codes
- Electrical Code Articles
- Electrical Code Directory covering AFCI circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, electrical GFCI, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-code, smoke-detectors.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wiring!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester, [amazon.com], I use for the detection of Standard Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
|« Help With 4 Way Switch Wiring||How To Replace a Phone Jack »|