» Residential Electrical Wiring: Guide to Home Wiring
» Need Electrical Help? Get a Quick Reply! Ask the Electrician
Portable generators and electric water heaters
By Dave Rongey
Summary: Electrical Generator Question: Hi Dave I am in the planning stage of installing a portable home generator. I will be using a 65KW unit.
Portable Generators and Electric Water Heaters
Hi Dave I am in the planning stage of installing a portable home generator. I will be using a 65KW unit.
Most of the generator descriptions say that they are not suitable for use with hot water heaters and other things. Is this a blanket caution to prevent civilians from overloading their generators and causing warantee problems, or are generators not able to handle the momentary very high inrush current that occurs when a large heating element gets up to temperature?
I know nothing about how generators regulate themselves. I find the NEC a hard read. Does national or BOCA code prevent the use of separate branch circuits that are connected only to the generator?
I have seen such in Hospitals where there are red outlets in the wall that are generator connected only. I live in manufactured housing where this would be a much simpler way of doing the room and office wiring.
Thanks- Ray the civilian.
Hi Ray - Great Electrical Repair Question.
Due to the high consumption a electric water heater requires it is always recommended that water heaters are either not wired as one of the generator loads, or that the water heater be replaced with a gas fuel unit when prolonged outages are expected.
The same goes for any high wattage electrical appliance such as electric ranges and ovens as well. The load that is placed on the generator is substantial and lasts for a duration of time, depending on the size of the device. Problems can occur if a load such as this is present and then a motor is started such as a refrigerator, freezer, well pump or a septic pump which is typically 120 volts.
These motor loads have a higher inrush of current at the start which can place an unbalanced load on the generator, possibly causing an overloaded condition. An oversized generator can be installed to compensate for these loaded conditions while planning for a worst case scenario where the loads hit all at the same time, but this may prove to be costly.
I am not aware of any code that would prohibit any type of load being placed upon a generator. The generator size needs to be determined by the expected loaded conditions.
The generator manufacturer may prohibit some loads due to the design capabilities of the generator. That being said, portable generators are typically not designed for higher loads so you may be forced to consider a more substantial Stand-By generator for your power requirements.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.