# Electrical Circuit Capacity

 By Dave Rongey Summary: A shop is set up in a storage unit and they have tapped their electrical into one of two 20A GFI circuit breakers starting from a sub panel at the building.

Check Out What Others Are Sharing at Ask the Electrician:
I like it.. Ron from Houston, Texas

## How to Install and Wire a Sub Panel

### So Keep Watching So I Can Help You Wire it Right!

Question From Michael P-
I have a woodworking shop set up in a storage unit and have tapped my electrical into one of two 20A GFI circuit breakers stemming from a sub panel on my building.

Upon investigation of the electrical set up, I have looked into the sub panels of my building and the two previous(Out of 7 buildings between myself and the main breaker panel) and found that each building has a panel that has a breaker linking it to the next in line.

Two buildings before mine feeds 2-20A circuits, one GFI for the receptacles and one for the 70W HPS lighting circuit, and one 50 A breaker that feeds the building just before me. The building just before me has the same 2 20A circuits as the previous and then has a 40A breaker that feeds the panel on my building.

My building has instead of 2 20 circuits, 4 20A circuits, two of which are GFI protected. And all of this is being fed from a 40A breaker in the previous sub panel? I don't have a complete electrical understanding, but his couldn't be right could it?

We are having trouble with having enough power on our circuits in the building sometimes depending if someone is using electricity further down in the facility. Is there any fix by increasing the size of the breakers down the line?

Hi Michael - Great Question!
No - increasing the size of the circuit breaker is not the answer. Increasing the capacity of the circuit by installing larger wire is, but this must be supported all the way back to the main panel that supplies the power for all.

It sounds like the whole system needs to be reconfigured based upon actual loads that are being connected throughout and then upgrading the supplying circuit. From my experience, storage units supply only enough power for lighting to each unit. If the breaker size is increased without increasing the size of the wire then there will be a high risk of fire due to overheating the existing wire size.

Thank you for your response, that was what I had kind of figured but didn't want to hear due to the inconvenience. They have several 70w HPS High Pressure Sodium ballasts that have been burned out and not replaced for a long time now, so I am sure they WILL NOT spend any money money on an upgrade. So the 40A on the previous panel feeding the 4-20A circuits on mine is not a problem?
Michael P

Michael,
A first hand inspection of the panels and the circuits would need to be done to fully determine if there is a problem with the 40 amp circuit.
Dave

## Home Electrical Wiring

### Helping You Wire it Right

NOTE: A List of All my Helpful Videos
Will Display at the End of This Video

## Learn more about Home Electrical Wiring with my online Video Course:Basic Home Electrical Wiring by Example

Be sure to get your copy of my BIG New eBook:

Complete Guide to Home Electrical Wiring

Wire It Right with the help of my Illustrated Wiring Book
Great for any Home Wiring Project.

## See How to Wire it Right!

Perfect for Homeowners, Students and Electricians
Includes:
Home Electrical Wiring - Room by Room
120 Volt Circuits
240 Volt Circuits
Multi-Wired Circuits
Wiring Methods for Installing Home Electrical Circuit Wiring
Electrical Codes for Home Electrical Wiring
....and much more.

## The Safest Way to Test Electrical Devices and Identify Electric Wires!

The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.

## The Quickest Way to Check for Faulty Electrical Wiring!

The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.

## Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!

The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..

The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.

### More about Electrical circuit capacity

Baseboard Electric Heater Circuit Wiring
Can I Put More Than One Set of Baseboard Heaters on the Same Circuit Breaker? How to Install a Baseboard Heater, Electrical Circuit Wiring.

How to Install an Electrical Sub Panel
Thinking about installing a Sub Panel? Here is what must be considered first, and you may find that you really do not need a sub panel at all.

Generator Transfer Switch Using Circuit Breakers
Can You Make a Generator Transfer Switch Using Circuit Breakers? How to Use a Circuit Breaker Interlock Kit for a Generator Transfer Switch.

Electrical Wiring and Landlord Tenants Rights
We keep tripping a breaker and found that 7 lights and plugs all run off the GFI plug in the bath room. The apartment is about 60 years old. Is this electrical wiring normal?

Connecting A Generator To A Home Video
How should I install the wiring to connect a generator to my home? Planning and Installing a Generator with a Transfer Switch: How to Connect a Generator to a Home.

Electrical Question from Martin about 240 Volt Wall Heater Wiring
Will 12-2 wire and a 20 amp breaker handle a 4000 watt 240 volt wall heater?

Can I Use A Remote Control Switch For Lighting?
How to Wire a Remote Control for Light Fixtures: Installing a Control Module, Wiring the Control Devices, Security and Monitoring Options.

How Many Electrical Wires In a Junction Box
How to Wire a Junction Box: Selecting a Junction Box for Electrical Wiring, The Basics of Electrical Junction Boxes, The number of wires that are allowed in a Junction Box.

electrical circuit capacity - 1512