Wiring a Single Outlet From a GFI
How to Extend Electrical Wiring to a Single Outlet From a GFI when the circuit appears to be wired by the feed through method.
Extending Off The Line Side of a GFI Outlet
Electrical Question: I purchased a wine cooler, Frigidaire LFWC18T6LB, which would not turn on.
- Reading the troubleshooting section of the manual I find that it cannot work on a GFCI circuit.
- Upon investigation I find that the circuit appears to be wired by the feed through method.
- When the wine cooler is plugged in the GFCI outlet across the room is tripped.
- Can I disable a single outlet to allow the wine cooler to operate?
This electrical question came from: Peter, a Handyman from Prescott Valley, AZ.
Additional Comments: Great Information!
How to Extend Electrical Wiring to a Single Outlet From a GFI
Application: Adding a 120 Volt Outlet.
Skill Level: Beginner to Intermediate. This electrical repair project is best performed by a Licensed Electrical Contractor or Certified Electrician.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and the number of outlets that will be added and the access to the location for the new outlets.
Precaution: Identify the existing outlet circuit power source, turn it OFF and Tag it with a Note before working with the wiring.
Notice: Installing additional outlet wiring should be done through the local building authority, installed according to applicable local and national electrical codes, with a permit, and have the required inspections.
Thanks for your electrical question Peter.
- Yes you can wire off the Line Side of the GFCI Outlet and extend the wiring to the wine cooler.
GFCI Outlet Wiring
Wiring GFCI Outlets
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
Electrical Outlet Wiring
Wiring Electrical Outlet for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Wiring GFI Outlets and Home Electrical Wiring:|
|« Previous||Next »|
|Replacing Outlets Without Ground Wires||Combo Switch and Outlet Wiring in Bathrooms|