Wiring a Bathroom Exhaust Fan Light Combo
How to Install Wiring for a Bathroom Exhaust Fan – Bathroom Exhaust Fan Heater Electrical Wiring – The white neutral wires would be tied together at the wall switch box. Understand that this is a typical wiring scenario, however the actual wiring connections may be different for your specific unit.
Switch Wiring for a Bathroom Exhaust Fan light Heater Combo
Bathroom Exhaust Fan: Hey Dave. I am taking out a fan and light combo and I’m replacing it with a fan, light and heater.
- I have 12/3 and want to know were do I put the commons?
- I have a rocker switch for the fan and light and I want the heater on a timer switch I want to make sure I am doing this right.
This electrical question came from: Stan, a Handyman from Mishawaka , Indiana.
Additional Comments: Love the site and tips.
Thanks for your electrical question Stan.
How to Install Wiring for a Bathroom Exhaust Fan
Application: Bathroom Exhaust Fan with Heater.
Skill Level: Intermediate to Advanced, best installed by a licensed electrical contractor.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and the access to the wiring for the wall switch for the exhaust fan and if a larger switch box will be required.
Precaution: The combo bathroom exhaust fan circuit should be identified, turned OFF and Tagged with a Note before working with the wiring and installing the fan speed switch.
Notice: Modifying existing wiring or installing additional bathroom electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
Bathroom Exhaust Fan Heater Electrical Wiring
- If the power source is at the wall switch then the commons or neutrals tie together and are not switched.
- If the 12/3 has been installed between the wall switch and the combo unit then because this combo unit has three switched functions then you will need an additional 12/2 cable installed.
- The wiring could then be where the black wire of the 12/2 could be for the heater function, which would be controlled by the timer switch, and the 12/3 could be wired so the black wire is for the light and the red wire is for the exhaust fan.
- The white neutral wires would be tied together at the wall switch box. Understand that this is a typical wiring scenario, however the actual wiring connections may be different for your specific unit, especially at the unit connections as well because some units have built in heat sensors which control fan operations to prevent the unit from overheating.
- It all depends on the specific bath exhaust fan and light combo unit you choose, so you must consult the installation manual and wiring directions.
- You may also see that the unit requires a dedicated circuit depending on the type of heating system the unit uses.
The Following Resources will assist you with your Bathroom Exhaust Fan
Bathroom Exhaust Fan Wiring
- Answers to all of your questions about installing a bath exhaust fan
and your bathroom exhaust fan replacement project
Wiring a Light Switch – Diagram 1
- Fully Explained Light Switch Wiring Diagrams.
- Detailed Electrical Wiring Diagrams and Pictures assist your Home Electrical Projects.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Exhaust Fan Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Power Adapter for a Nintendo DSi Video Game||Safe Locations For Electric Dryer Outlets|