Understanding Multi-Wire Circuits
Circuits four and eight share the same neutral wire, is this correct?
Multi-Wire Circuits and Shared Neutrals
[ad#block]Question: Circuits four and eight share the same neutral, is this correct?
This electrical question came from: Marvin , a Student from San Diego, California.
See more about Home Wiring for California
Thanks for your electrical question Marvin.
Multi-Wire Circuit Wiring
- Marvin, if the circuit breakers are full size then no, this is not correct.
- A multi-wire circuit that shares the same neutral must have each of the two circuits on separate buses, the circuit breakers must be side by side, and the circuit breakers must be have their handles tied.
- Typically a 2-pole circuit breaker is installed.
- This will ensure that each of the two circuits voltage is correct, and the neutral wire load is balanced properly between the two circuit wires.
The Following links will assist you with your electrical question:
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
For more information about 220 Volt Wiring Diagram
220 Volt Wiring Diagram
Wiring 220 Volt Electrical Outlet
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how electrical outlets for the home are wired.
This link is helpful as a Student
Electrical Code Articles
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Multi-Wire Circuits and Home Electrical Wiring:|
|« Previous||Next »|
|Replacing a Faulty Dimmer Switch||Basement Circuits and Electrical Wiring|