Electrical Problems after a Lightning Storm with Plugs and Dryer
After a lightning storm, some plugs don’t work and the dryer tries to come on, but will not start.
The Dryer is single phasing and certain other wall plugs are out after lightning storm.
The dryer tries to come on but doesn’t have enough power to start.
We looked in the circuit box and nothing is tripped.
Is this repairable by us or do we need an electrician?
- I will begin by stating that I advise homeowners not to perform work In their main Electrical Service Panel, especially when it come to trouble shooting the loss of the Main Service or part of it.
- The extent of which you can safely perform checks would be visually inspecting the breakers to see if they are tripped. In some cases a breaker may appear to be in the “ON” position when in fact it is tripped off internally. If this is the case, then by turning the breaker “OFF” all the way, then back “ON” should remedy this situation, otherwise there may be another problem, and it still may be with the breaker or the attachment of the breaker to the Panel Buss. After making these Visual Checks, if you do not have Normal 240 volt Power, then I would consult a Professional Electrician.
- The typical home has a 240 volt service, which is a result of two 120 volt lines entering the Main Panel from your Local Electric Utility Company. It appears that you have indeed lost one of the 120 volt lines.
A test must be performed to discover where the trouble is. This comes through a Process of Elimination and Inspection, starting with the Main Service Feeds entering the breaker area of the service – NOT inside the Electric Utility Company area of the panel (this area is off limits to anyone while the electrical service is energized from the utility company).
- The process usually starts by checking at the Main Breaker or any 240 volt breaker – Using a tester that can test for 240 volts, checking Line One across to Line Two – this area should have 240 volts on the secondary side of these breakers. If the reading does not show 240 volts then the problem is on the Electric Utility Company side of your service and you will need to call the Utility Company and explain the situation to them.
Be Safe and Be Careful,
I hope this helps you!
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Partial Power Questions and Home Electrical Wiring:|
|« Previous||Next »|
|Electrical Problems after a Lightning Storm Damages the Dryer||Question – 200 Amp Main Circuit Breaker Tripping – Part 3|