Split-Buss Electrical Panels
Understanding Split-Buss Electrical Panels: Dave explains that a split buss circuit breaker panel allows the upper circuits to remain energized while the bottom section is controlled by a separate circuit breaker.
Understanding Split-Buss Electrical Panels
[ad#block] Electrical Question: Dave, the attached picture is a my breaker box in my home. The top two breakers are 50 amp and are 240 Volt.
- The next one is a 30 amp 110. The other six breakers are 20 amps and they are for lights, outlets, etc.
- When I throw the 30 amp, the whole house is dead except the two 50 amp lines, as the 30 amp is my main breaker (the 50 amp lines have nothing plugged into them). Why is this?
- When you throw the main should it shut off power to everything?
- Also is the 30 amp main big enough for those 6 20 amp breakers?
- I seem to blow the 30 a lot during the summer running two room-air conditioners
This electrical troubleshooting question came from: Larry, a Homeowner from Linwood, MI
See more about Home Wiring for Michigan
PLEASE NOTE: The following information applies to this question only. In normal situations circuit breakers should never be exchanged for a larger size.
Thanks for your electrical troubleshooting question Larry.
Understanding Split-Buss Electrical Panels
- Larry, you have a split buss circuit breaker panel which allows the upper circuits to remain energized while the bottom section is controlled by the 2-pole 30 amp breaker. The wires size linking the 2-pole circuit breaker to the bottom section of the panel will support a larger size circuit breaker, in fact one of the 2-pole 50 circuit breakers could be swapped with the 2-pole 30 amp circuit breaker allowing more amperage to the bottom section of this panel.
- A split buss panel such as this is not common for most homes these days, but for this application at one time it allowed the upper 2-pole circuits to remain on where they may have fed large equipment that was required to remain on while the lower circuit were turned off.
- One common application for a similar set up would be for a 2-pole circuit to remain on for a well pump where in the case of a fire all the electrical circuits can be De-energized but the water supply or pump remains energized.
The Following will assist you with Home Electrical Systems
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Panel Circuit Listing
Electrical Wiring Protection using Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Troubleshooting, Split-Buss Panel and Home Electrical Wiring:|
|« Previous||Next »|
|Half Hot Switched Outlets Explained||Light Fixtures and Three Way Switches|