# Sizing a Generator Transfer Switch

 Here are the Steps for Sizing a Generator Transfer Switch: The rating and size of all the electrical components of the system should be sized properly.

## Hooking Up a Generator to the House Panel Using a Circuit Breaker Interlock Kit for Backup Power

NOTE: A List of All my Helpful Videos
Will Display at the End of This Video

with my online Video Course:
Basic Home Electrical Wiring by Example

The Importance of Sizing Generator Transfer Switches
Electrical Question: If I have a 50 amp inlet can Reliance Model 31410B 10 Circuit Transfer Switch, is it rated for 12,500 watts? My electrician installed a Reliance Pro\Tran Model 31410B 10 Circuit Transfer Switch that says its a 30AMP, but he says it is the same as the 50AMP 51410B. Is this true? Will I still be able to pull in 12,500 watts? The inlet does plug into my 50AMP out on my generator but I don’t have a watt meter to verify

This electrical question came from: Steven, a Homeowner from Washington Township, Michigan.

Thanks for your electrical question Steven.

### Sizing Generator Transfer Switches

Steven, lets do some basic math here and you will see for yourself what the rating is:

## The Steps for Sizing a Generator Transfer Switch

To calculate watts, the formula is amps times volts.

• Examples, assuming your generator has a 240 volt output:
• 30 amps times 240 volts = 7,200 watts
• 50 amps times 240 volts = 12,000 watts

Steve, I will just say that you better have yourÂ  electrician explain his calculations to you, then compare the results to the rating of the equipment, along with the rating and size of all the electrical components to make sure your system is sized properly.

• It is essential to properly size the home generator, the transfer switch and electrical wiring and electrical components, and this size must be determined according to the anticipated electrical loads that will be placed on generator power.
• Identifying and understanding the types of loads is extremely important as well. For example an average generator should not be used for a typical well pump.

More about Generators and Transfer Switches:

• ### Home Electric Generators

• This series covers a wide variety of topics all about home generators including sizing, selecting, connecting and safely operating this all important addition to your home.

The following may also be helpful for you:

## Dave's Guide to Home Electrical Wiring:

» You Can Avoid Costly Mistakes! «

Wire It Right with the help of my Illustrated Wiring Book
Great for any Home Wiring Project.

## Complete Guide to Home Electrical Wiring

Perfect for Homeowners, Students,
Handyman, Handy Women, and Electricians
Includes:
Wiring GFCI Outlets
Wiring Home Electric Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring Light Switches
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshoot and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
NEC Codes for Home Electrical Wiring
....and much more.

## Learn more about Home Electrical Wiring with my Online Video Course:Basic Home Electrical Wiring by Example

Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.

## The Safest Way to Test Electrical Devices and Identify Electric Wires!

The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.

## The Quickest Way to Check for Faulty Electrical Wiring!

The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.

## Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!

The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..

The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.

 More articles about Generator, Transfer Switch and Home Electrical Wiring: « Previous Next » How to Add a Ceiling Light Fixture Garage Wiring and Electrical Service Panel

4 Responses to “Sizing a Generator Transfer Switch”
1. Gene says:

Bid to add a Generac-6462-16,000W + 200A Service Entrance Transfer Switch (RTSY200A3) into an existing house wiring system. Electrical contractor’s bid states: ‘Current utility service is 100Amps and the generator transfer switch is 200Amps. We will have to install a new 200Amp Service Entrance Meter’ Where is this scenario described in the NEC documentation? Would you agree this is a required step? The matching of utility service and transfer switch ampacities is necessary to meet code and inspection?

2. Dave Rongey says:

Hi Gene,
Installing a Generator and Transfer Switch
Without knowing all of the details about this project, it would be interesting to note that the size of the transfer switch should be based upon the maximum capacity of the generator. A quick calculation shows that this generator produces under 100 amps, (16,000 watts / 240 volts = 66.66 amps) so my question is why a 200 amp rated transfer switch when 100 amp transfer switches are available.
It is always a good idea to get two or more bids for a project such as this, no doubt you will receive more clarification.
I hope this helps,
Dave

3. Joe says:

I have 200 amp service to the house and a 6000 watt generator. The generator needs to only supply 40-50 watts to the house. What size manual transfer switch do I need? The generator and the electrical service does not go directly to the house but to a farm pole where I split the incoming power to three out buildings and then to the house.
Joe

4. Dave Rongey says:

Hi Joe,
For your safety, and to make sure the installation is up to current NEC Codes, generator projects such as this are best planned out with an on site evaluation by a licensed electrician who can work with you to make sure all aspects of the project are taken into consideration.
Be Safe,
Dave