Replacement Ceiling Fan Wiring Configurations
How to Fix Ceiling Fan Wiring Problems: Common Problems with Ceiling Fan Wiring and How to Fix Them, Identify the Ceiling Fan Wires for the Right Connections, Wires for Ceiling Fan Light Fixtures, Wiring Connections that Cause a Tripped Circuit Breaker.
Guide to Wiring Connections when Replacing a Ceiling Fan
Electrical Question: I replaced a ceiling fan and when I turned it on the light worked but when I pulled the chain for the fan the circuit breaker tripped off.
- I just installed a ceiling fan with a light to replace a similar unit.
- There were 3 wires coming from the ceiling that are white, green and black, and the same 3 colors coming from the fan.
- I connected all like colored wires together, and screwed in the motor. Then, I connected 2 more sets of wires, this time, the wires ended in plastic blocks that were supposed to connect to each other.
- All seemed to go well. The light turned on immediately, but when I pulled the chain for the fan, there was a small spark from the fan and the breaker was tripped.
- The light continues to work, but nothing from the fan, but consequently, one of our 3 outlets on the same circuit no longer works as well.
Any help would be greatly appreciated!
This electrical wiring question came from: Megan, a Homeowner from Brooklyn, New York.
Thanks for your electrical repair question Megan.
How to Fix Ceiling Fan Wiring Problems
Application: Wiring a Ceiling Fan.
Skill Level: Intermediate to Advanced, Best performed by a Licensed Electrician or Electrical Contractor.
Tools Required: Basic Electricians Pouch Hand Tools, a non-aluminum ladder and Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and access to the switched outlet wiring and the location for the replacement ceiling fan.
Precaution: Identify the ceiling fan and outlet circuit, turn it OFF and Tag it with a Note before working with the wiring
Common Problems with Ceiling Fan Wiring and How to Fix Them
- Identify the Ceiling Fan Wires for the Right Connections
- Megan, the two wires that you mention as supposed to be connected to each other may be the problem.
- The last wire connections should be taken apart until you can identify the wires as described in the installation manual that came with the ceiling fan.
- Wires for Ceiling Fan Light Fixtures
- Some ceiling fans come with pre-wired connections for an optional light kit which may not be installed from the factory.
- The wiring for the optional light fixture should be capped off and not connected.
- If desired, a compatible light fixture may be added to the ceiling fan and wired to the provided wires.
- Wiring Connections that Cause a Tripped Circuit Breaker
- Connecting a Power wire and a Neutral wire together will cause a direct short.
- If this is the case with your ceiling fan then connecting the last two wires together may have cause a direct short which would cause the circuit breaker to trip off.
- Separate the two wires and cap them off with a wire connector.
More about Wiring a Ceiling Fan
- Wiring ceiling fans
How to Install and Wire Ceiling Fans
Take the mystery out of ceiling fan wiring. Ceiling Fans are a great way to lower your energy bill and brighten up one of your favorite rooms.
- The most commonly asked questions about installing Ceiling Fans, controls, light ceiling fan fixtures and other ceiling fan wiring questions and answers.
Installing a Ceiling Fan
Ceiling Fan Installation
- This series of photos show the electric wire to ceiling fan box, preparing to mount the ceiling fan box,wire into the ceiling fan box through a wire bushing, attaching the ground wire, mounting the cradle bracket, the ceiling fan wires are connected, close the canopy, attach the fan blades and wiring a double stack switch,installing double stack switch, and explain how to connect the ceiling fan wiring blue wire.
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Repairs, Wiring Configurations and Home Electrical Wiring:|
|« Previous||Next »|
|Electrical Circuit for a Tanning Bed||How Many Receptacle Outlets Are Allowed Per Circuit|