Installing GFCI Protection for a Hot Tub
WHEN INSTALLING WIRING FOR AN OUTSIDE HOT TUB AM I REQUIRED BY CODE TO INSTALL A GFCI IN BOTH THE INDOOR PANEL TO PROTECT THE WIRING AND IN THE DISCONNECT…
Electrical Question from DEREK about 220 Volt GFCI Wiring for a Hot Tub
Background: DEREK, a Electrician from EDMONTON ALBERTA CANADA
[ad#block]Question: WHEN INSTALLING WIRING FOR AN OUTSIDE HOT TUB AM I REQUIRED BY CODE TO INSTALL A GFCI IN BOTH THE INDOOR PANEL TO PROTECT THE WIRING AND IN THE DISCONNECT 3 METERS FROM THE HOT TUB OR IS JUST ONE IN THE MAIN PANEL SUFFICIENT
Additional Comments: I HAVE BEEN EMPLOYED ALL MY WORKING LIFE INSTALLING MAINLY EXPLOSIVE PROOF EQUIPMENT IN HAZARDOUS LOCATIONS SO IT IS GOOD TO HAVE AN EXCELLENT REFERENCE SITE LIKE YOURS WHEN DOING OTHER ONE OFF JOBS(FOR MY DAUGHTER)
Thanks for your electrical question and encouraging comments Derek.Â The GFCI Protection is typically installed at the location of the Hot Tub . This makes it convenient for testing. A standard circuit breaker is fine for protecting the circuit from the source panel to the location of the GFCI disconnect at the hot tub.
Explosion proof work is really something, I just installed some the other day. I’m glad this website is helping electricians as well.Â I know there are a lot of commercial and industrial electricians who are working at the residential level and I know the adjustments that these people will be going through.Â Residential work is more tedious compared to industrial.Â I actually miss working in a large industrial facility.
The Following links will assist you with your electrical question:
For more information about 220 Volt Wiring Diagram
220 Volt Wiring Diagram
This link is helpful as a Electrician
Electrical Code Articles
Make sure not to miss these Resources for: How-To-Videos
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about 220 Volt Wiring, Hot Tub and Home Electrical Wiring:|
|« Previous||Next »|
|Sizing a Home Generator Transfer Switch||Ethiopia Residential Wiring Diagram|