How Bad Advice Can Burn Your House Down
How to Wire an Electric Kiln and How NOT to Wire an Electric Kiln.
A Classic Example of Bad Advice
Question: I have a kiln with a 6-50plug. The kiln is: Operating Voltage: 240V (208V and 3 phase available)
Amperage: 40A Watts: 9600W
I read on a website that I could build an extension to connect it to my Dryer outlet which has a 10-30r. The Dryer breaker is 50A. I know that 50A to 30A extensions are available at RV and Welding resources, but are expensive and have slightly different plugs or receptacles than what I need, so I am making my own.
I have a 6-50r, connected to 25? of 10/3 wire(black, white and green) at one end and a 10-30p at the other. The black and white wires are attached to the side blades on both ends and the green to the center ones.
The Dryer wall outlet has black, red and white wiring. When I plugged it in(not yet attached to kiln) it not only tripped the Dryer breaker, but the main breaker also. I took apart both ends and saw that the white and black wires on the 10-30p were attached opposite from the Dryer outlet. I switched them and plugged it in again. It tripped the Dryer breaker but not the main. Again nothing is connected to the kiln. It blows the breaker as soon as plugged in to dryer outlet.
What am I doing wrong?
Also on the 6-50r the wires are held directly in place with 2 large copper screws and one silver one, with no plate in between the screws and wire.. Is this correct?
This electrical question came from: Bobby, from Scottsdale, Arizona
Additional Comments: Thank you
Thanks for your electrical question Bobby
Incorrect and Hazardous Kiln Wiring
Understand Electrical Circuits and Prevent a House Fire
- A 30 amp dryer circuit can safely provide no more than 30 amps, and it can NOT safely provide 9600 watts to your kiln without damaging the electrical circuit.
- The 240 volt home dryer circuit should never have a circuit breaker installed that is larger than 30 amps otherwise the circuit could overheat to the point where there will be damage to the circuit wiring and components and could become a fire hazard.
- Because of what has been described I would highly recommend that the circuit be shut OFF and a Qualified Electrical Contractor be called to inspect the circuit for damage.
- Any wiring that has been done for the kiln should be checked as well and then compared to the nameplate or specifications of the kiln.
- If the 30 amp 240 volt dryer circuit has been used for the kiln then it may be damaged and need to be replaced as well.
- The adapter that you have described is incorrect and should not be used. The connections of the adapter are incorrect which is causing the circuit to trip OFF.
How to Wire an Electric Kiln
- From what has been described this 9600 watt 240 volt kiln will require a separate dedicated 50 amp 240 volt circuit.
RV 50 Amp Cord Adapters
The RV cord adapters that you have described are designed to safely provide 30 amps of power from a 50 amp circuit, NOT 50 amps of power from a 30 amp circuit – there is a BIG difference because the 30 amp circuit cannot provide 20 extra amps of power, and if it is attempted it will create a hazardous condition.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
3-Wire and 4-Wire Configurations for Clothes Dryers
See an electric dryer installation with a typical 220 Volt electric power cord wiring system. You may find yourself with either a 3-wire or 4-wire electric dryer, or a 3-wire or 4-wire outlet. Lets look a how the electric dryer is wired and what to do if your cord does not match the plug.
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Electric Welder Circuit Sizes||Generator ATS Provides Power During Partial Power Loss|