How To Wire Half Hot Receptacles
Vince in New York asks: I have a receptacle where 3 pairs of 14-2 lines enter the outlet box, how should this be wired?
Wiring Diagrams for Half Hot Receptacles
[ad#block]Electrical Question: I have a receptacle where 3 pairs of 14-2 lines enter the outlet box, how should this be wired?
- One pair of Wires is the feed.
- The second pair goes to a switch on the wall to control a light. (the brass tab is missing, thus making this a half hot receptacle).
- The third pair go to another receptacle on the other side of this wall.
- The wires were back stabbed except for the black feed and a white neutral (I believe the neutral goes to the switch) Both the black feed and white neutral are connected to the same screw.
Here is the Problem:
- The switch on the wall does not work. (I replaced the switch, still nothing)
- The light that is plugged into this outlet is plugged into the side of the receptacle that the black feed is connected to.
- The light works when it is plugged into the receptacle. But the switch does nothing.
How should this be wired?
This electrical wiring question came from: Vince, a Handyman from Amherst, New York.
See more about Electrical Wiring for New York
Additional Comments: I love the website!
Thanks for your electrical wiring question Vince.
Wiring Diagrams for Half Hot Receptacles
Skill Level: Intermediate to Advanced.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and install electrical circuit wiring.
Precaution: Identify the receptacle circuit, turn it OFF and Tag it with a Note before working with the wiring.
- A full set of wiring diagrams can be found using the links below.
- See the diagrams about half-hot and switched outlets.
Wiring Electrical Outlet for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
How to wire a switch
Wiring a Light Switch – Diagram 1
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring, Switched Outlet and Home Electrical Wiring:|
|« Previous||Next »|
|Electrical Question about a HVAC Unit That Trips The Circuit Breaker||Installing Underground Wiring for a Shed|
I am wiring half hot receptacles with the other half of the receptacle being on a gfci. when I turn power on to GFCI, the red light comes on, as soon as I push the test button it trips the gfci. I have been down the line, 5 outlets with a outlet tester and is shows all the outlets are wired correct. Can you help?