How to Stop Fluorescent Lights from Flickering
Solving the Problem of Flickering Light Fixtures: How to Stop Those Annoying Flickering Fluorescent Lights, The Main Causes of Flickering Fluorescent Lights and How to Fix Them
Guide to Solving the Problem of Flickering Light Fixtures
Electrical Question: Is it normal for a fluorescent light fixture to constantly flicker during a brief time when in use?
- T8 Light Fixture and Switch
One of our offices utilizes a 3 tube 120volt T8 fixture in one of the lavatories. This facility uses an emergency 12/24v battery backup lighting system throughout, this room included. Room lighting is controlled by a single throw switch that also controls the ventilation fan. As a staff use only room, lighting is generally off, requiring a “cold start?, causing constantly flickering during the brief time in use. If left on, they stabilize, brighten normally and no longer flicker.
- Replaced the Tubes
So far my electrician has replaced the tubes, bypassed the emergency system, replaced the main ballast and recently disconnected the fan circuit in an attempt to eliminate it as an interference source. Still we have no positive results. We are considering replacement of the fixture at this point, but fear the concern will still be present following.
- Light Fixture in a Cold Room
Is this a normal system characteristic until warmed and this particular fixture is simply mis-matched for the application, or are there other factors we are overlooking? I have great confidence in my electrician’s ability to diagnose, but even he is baffled. Although we have not inspected yet, I thought maybe the air conditioning duct work in the attic may be too close to the fixture and super-cooling the ballast/tubes, in which case insulating the duct work may correct the concern.
Should we just install a different type of fixture better suited to this short time use application?
We are both baffled, can you offer some advice?
Thanks in advance for your help!
This electrical wiring question came from: Mark, from Denver, Colorado.
Background-Facility general maintenance & repair technician for a group of physician offices.
NOTE: Mark’s Electrical Skill Level is Novice, with the ability to do minor service, test circuits, replace tubes and ballasts, switches, receptacles, dimming fluorescent systems. The facility extensively uses 277 volt, as well as 120volt systems. He has no certifications, but he uses a proven licensed electrical subcontractor for tasks beyond my capability.
Thanks for your electrical wiring question Mark.
How to Stop Flickering Fluorescent Lights
Application: Fluorescent Light Fixture
Skill Level: Beginner to Intermediate – Best if performed by a Licensed Electrical Contractor.
Tools Required: Basic Electricians Pouch Hand Tools, a non-aluminum ladder and Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and access to the light fixture(s).
Precaution: Identify the light circuit, turn it OFF and Tag it with a Note before working with the wiring.
Notice: Installing additional fixture wiring should be done according to local and national electrical codes with a permit and be inspected.
The Main Causes of Flickering Fluorescent Lights and How to Fix Them
- Replacing Lamps Before They Burn Out
If the lamp has dark circles at the ends and needs to be replaced. If the lamp is allowed to burn out in the socket it may cause the ballast to burn out and then it will need to be replaced as well.
- Replace the bad lamp right away.
- Align the Lamp Pins in the Sockets
Both pins of the lamp are not positioned into the socket properly. This will cause the lamp to burn out prematurely and flicked as well.
- Make sure to align the pins when installing the lamps.
- Install the Right Lamps
The wrong lamp has been installed and does not match the ballast specifications.
- Install the right lamp.
- Grounding the Light Fixture
The light fixture is not properly grounded.
- Install a ground wire and bond it to the metal frame of the light fixture.
- Cold Areas and Flickering Lamps
The light fixture has the older magnetic ballast which does not perform well in cold areas and will make the lamps flicker until they warm up.
- Replace the ballast with an electronic ballast that is rated for cold areas and install the specified lamps.
More about Home Wiring and Light Fixtures
How To Install Recessed Lighting
Installing recessed lighting for your home electrical improvements. Discover how recessed lighting can enhance the mood of any room in your home.
Repairing Electrical Wiring
Repairing Electrical Wiring
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical and Home Electrical Wiring:|
|« Previous||Next »|
|Planning Pump House and Well Circuit||How to Correct Light Switch Wiring that Does Not Work|
I have 15 year old 48 inch fluorescent light fixtures in our walk-in closets. The lights in one closet are very dim and flickering. One of them has a 3 inch dark spot on one end. I replaced both lights and only one will come on very dimly. Also, it’s flashing on one end. Since this fixture has no apparent starters, would this indicate a bad ballast or some other problem?
Make sure the pins of the lamps are set all the way up into the sockets. If the lamps are properly installed and they will not light up all the way then the ballast will most likely need to be replaced.
I hope this helps,
I have just replaced my two florescent bulbs, being 48″ 34 watts and 1 1/2 inch width. They seem to run fine until about ten minutes, then they begin to flicker really bad.
Any help is greatly appreciated.