» Need Electrical Help? Ask the Electrician
How to Install Electrical Wiring in a Livestock Area
Electrical Wiring Installation Methods for a Livestock Area – The structure electrical wiring should be installed in protective conduit and weather proof boxes, enclosures and covers must be installed.
Electrical Wiring Method for a Livestock Area
[ad#block] Electrical Question:I need some advice on mapping out a new electrical circuit for my chicken coop.
The framing is done, before I insulate I want to put in my boxes & wiring.
Here is the basic wire I am using and what I want in this circuit.
Using 12/2 & 12/3 Yellow Romex wire
4 inside outlets (one on each wall) One of these outlets I want controlled by a switch.
1 overhead light box, center of ceiling, contro1led by a switch
1 outdoor outlet, and 1 outdoor light(will require a switch)
3 Switches to left of door entry.
I need help on where the the power feed should enter this circuit, and explain what type of wire loops need to be created ?
I am planning on feeding this circuit from the power panel in my barn. Using a 20Amp GFI/Arc Fault breaker, running
12/2 UF Cable thru conduit from the barn to the chicken coop. Any issues with running this whole circuit off of a GFI/Arc Fault breaker ?
I’ve done many of my own electrical projects in the past, but this is the first all new circuit.
Thanks for any and all information & replies,
This electrical wiring question came from: Clint, a Handyman from Keene, New Hampshire.
See more about Electrical Wiring for New Hampshire
Thanks for your electrical wiring question Clint.
Electrical Wiring Installation Methods for a Livestock Area
- A single 20 amp circuit that will feed a livestock area may be supplied from the electrical service panel of the home or nearest building with an electrical panel.
- The circuit must be protected by GFCI.
- A conduit may be installed into a trench that is 18 inches deep or the UF cable may be installed in a trench that is 24 inches deep and protected with conduit as it is routed up to the destination.
- UF cable does not need to be installed in a conduit, and if it was the conduit would have to be over sized.
- Romex wiring should not be used as described unless it is installed inside protected or covered walls and is permissible for the type of structure.
- The structure electrical wiring should be installed in protective conduit and weather proof boxes, enclosures and covers must be installed.
- The light fixtures should be a bulb type that is protected by a tempered glass enclosure with a protective cage covering.
- The circuit wiring would be installed and distributed according to the location of the receptacles and switches.
- A project such as this should be installed with a permit and inspected.
The Following will assist you with your electrical question:
Electrical Wiring Codes
Home Electrical Codes
Electrical Code Directory covering AFCI circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, electrical GFCI, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-codes and smoke-detectors.
Basic Home Wiring Diagrams
For more information about Wiring Diagram
Home electrical wiring diagrams are an important tool for completing your electrical projects. An electrical wiring diagram can be as simple as a diagram showing how to install a new switch in your hallway, or as complex as the complete electrical blueprint for your new home or home improvement project.
This link is helpful as a Handyman
The following may also be helpful for you:
Electrical Wiring Video #2
Home Electrical Wiring Videos about this Topic and More
Dave's Companion Guide to Home Electrical Wiring:
|More articles about Electrical and Home Electrical Wiring:|
|« Previous||Next »|
|Repairing Security System Telephone Wiring||Hot Tub Electrical Circuit Wiring and Requirements|
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.