How To Fix 4-Way Switch Wiring
How to Avoid Confusion about the White Wire and 4 Way Switch Wiring with the power and the 3-wire cable of the 3 Way Switches
How to Avoid Confusion about the White Wire and 4 Way Switch Wiring
[ad#block]Electrical Question: I have a 4 way switch wiring question.
- I have the first switch with the power and the 14/3 3 way wire so connect the neutrals and that one is done.
- The one I have trouble with is the 2nd box.
- I have the 3 wire from the 1st switch the 3 wire going to the 3rd box which is dead ended because I have the switch leg also going to the 2nd box?
- So there are two 14/3 wires and the 14/2 wire switch leg.
Please help me splice this.
Additional Comments: please need your help!
Background: Dan, a Other from Oroville, Wash
Thanks for your electrical question Dan.
4 Way Switch Wiring
- The neutrals should be spliced and pass through the middle switch box, then splice to the neutral wire that goes to the light fixture at the last switch box.
- You may experience challenges wiring the center 4-way switch.
- Pay close attention to the colors of the screws on the 4-way switch and understand that one set of wires are attached to one set of screws, and the other set of wires attach to the other set of screws.
- Getting this reversed is a common mistake that is made when wiring 4-way switches.
4 Way Switch Wiring
Fully explained 4 way switch diagrams. 4-way switches are a convenient way to operate lighting fixtures from three or more locations. The electrical wiring adds additional wiring to the same principles of 3-way switching.
Wiring a Light Switch – Diagram 1
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about 4-Way Switch, Electrical, Lighting and Home Electrical Wiring:|
|« Previous||Next »|
|Factors to Consider For Home Made Light Fixtures||How To Switch A Ceiling Fan Light Apart From The Fan|